How to improve the thermal oil 10 ton boiler efficiency oil boiler thermal efficiency is a lot of users are taken into account, we believe that this issue is the direction of each used in the production of various types of oil boiler manufacturers have been in the study. Many users at the time of the oil furnace to operate, often in the actual production process, we found some new problems, but all the problems, the headache is higher oil boiler flue gas temperature, low thermal efficiency the phenomenon that a serious impact on our work, then how should we do to improve the thermal efficiency of it? need to understand this is to meet the low-temperature characteristics of the thermal oil comes as synthetic heat transfer oil. However, the vast majority of synthetic HTF complex biphenyls, benzene derivatives of both components, or a vapor of volatiles has strong carcinogenicity, it is strongly recommended to select customers conducting oil mineral oil products. Second, conducting oil products to meet the low temperature performance process, but also have a relatively high flash point required. In general, oil engineers suggest, low flash point not lower than the HTF opening 200 ℃. After a professional manufacturer of continuous research and improvement of its equipment, in order to improve its thermal efficiency was found to be increased oil boiler heating surface of the tail, say, air preheater and economizer. But when organic heat carrier furnace return temperature is high, you can not set the economizer, air preheater can only be set to alleviate the situation. So if the oil boiler and not other low-temperature heating system heat exchanger, then the only way to improve energy efficiency is adding air preheater. After adding air preheater can be a corresponding increase in the flow rate of heat-conducting oil, oil boiler in order to ensure safe, reliable and stable work, the thermal efficiency of the boiler plant with thermal oil will be a corresponding increase.
Which one is simpler in structure for electric steam 10 ton boilers or gas-fired steam boilers? Electric steam boilers and gas-fired steam boilers, if the structure of the two boilers are compared, then the electric steam boiler is simpler, and the boiler price is lower. Because there are gas, smoke and storage systems in gas-fired steam boilers, the structure is more complex and the price is higher.
Jingdong, typical Chinese-style self-employed business enterprise, has its Jingdong Mall, Jingdong financial, Jingdong intelligence department. May 2014 in the US Nasdaq stock exchange officially listed. 2018 "Fortune" Global 500 list of the 181. Fast 10 ton boiler, A-class boiler manufacturing unit, Class 1 boiler installation company, more than 20 years dedicated to the development of clean fuel energy equipment, manufacturing and sales. The introduction of low nitrogen emission boiler is the first time in a market-oriented approach using FGR technology products, as guardian of the "APEC blue" gave their part.
How to prevent corrosion of the gas 10 ton boiler gas boiler it if the temperature is too high, some of the components of the boiler working long hours in the intense heat of the environment at work, the situation will cause boiler corrosion occurs. So, we are in the process of work what to do to reduce the corrosion of it? Here to tell you about some of the methods of preventing corrosion of boiler gas. Reason and approach demands on internal corrosion of the gas boiler must be in accordance with the methods and principles of conduct, you can now use a more extensive domestic and international gas boiler corrosion detection approach is magnetic flux leakage and ultrasonic detection. Ultrasonic Ultrasonic detection is used to measure the wall thickness after etching using the principle of ultrasonic pulse reflection. The basic principle of magnetic flux leakage method leakage flux detection method is based on the high-permeability properties of the ferromagnetic materials, magnetic permeability of the gas boiler corrosion disadvantage is much less than the permeability of the furnace, the applied gas boiler is magnetized in a magnetic field effect, when the furnace is no disadvantage, most of the magnetic lines of force through the pipe. Uniform distribution of lines of magnetic force at the moment; when the internal elbow has the disadvantage that the onset of meander lines of magnetic force, and a part of magnetic lines of force from leaking out of the outer steel pipe. Detecting the escaping magnetic flux leakage outer elbow, it can be determined whether the shortcomings exist. When the probe detects a straight guide hot oil furnace inner wall emit ultrasound pulse, to receive from the probe first reflected pulse within the outer wall, and will receive the ultrasound probe, this pulse and the pulse reflected from the outer wall of the outer appearance of the reflected pulse trip distance between the reflecting wall thickness. Gas-fired boiler in accordance with the practices and conditions set forth in the demand for the detection of practice, in accordance with the detection of ultrasonic inspection method can be distinguished way. High temperature components such as a gas boiler front panel, convection superheater and reheater temperature is the primary structural member and the like inside the boiler, a very long time to work in the harsh environment of use of the medium flame, smoke, ash, etc., and therefore the working process changes occurred in the organization and function of a range of materials, these changes hit the gas boiler creep, fatigue, corrosion, erosion and other messy aging and failure mechanisms. These high temperatures Microstructure component material will follow the extension of working time deteriorated creep damage occurs, such as loose pearlite, spheroidized carbides, grain boundary and growth mobilization, holes creep, intergranular cracking occurs .Free Chat
Copyright © 2020.Company name All rights reserved.