Three tempering tube 10 tons szs hot water boiler installation and commissioning of the structure outlined hot water boiler is fast loading of the internal combustion level. A second high temperature flue gas successively washed roots and refluxed for three breathing tube, the smoke chamber into the atmosphere through the chimney. Gas hot water boiler equipped with the world famous burner, combustion using automatic adjustment, automatically adjust the water supply, the program starts, automatic control and other functions. The boiler has a compact, safe, reliable, easy to operate, installation speed, low pollution, low noise, high efficiency. Widely used in enterprises, hotels, hospitals, office buildings, civil construction and other industrial steam, life, mining and other facilities. This installation requires fast speed boiler installation, installation is very simple, the boiler does not require special ground base, only enough to withstand the ground to power. 1. Install the water supply line requires the highest level reservoir, generally not critical, the high from the ground to the reservoir tank, underground tank of water should be kept clean. Pool water outlet. For wire entrance filter water supply line. 2, the straight cross-section is mounted, the return pipe return pipe to be 0.5 meters above the bend radius should be 4 to 5 times the diameter of the pipe, the pipe should be installed at the highest automatic steam valve to prevent the steam from the pipe loop. At the same time, the general requirements of the highest level possible reliable reserve pool. When the boiler water level is below the line, the water will flow into the boiler when the next time you start. Filter wire 3 should be installed at the outlet (i.e., the inlet pipe) of the pool. Installation requires a supply line Burner fuel hose has two interfaces, and for the oil return into the oil, as long as the boiler return oil chamber and the oil corresponding feed pipe. Dedicated hydraulic system from the boiler tank to the burner pump port, an operation instruction for the burner 4 is provided. Chimney straight chimney installation requirements. The length of the chimney should not be too long, the stack height should be less than 5 meters. Chimney height should comply with relevant standards. Chimneys should be added raincap and smoke. Weight not directly on the boiler chimney host chimney 5, hydrostatic test shall be carried out after the installation of boiler water pressure test supervisor. Pressure test before proceeding to deal with internal boiler inspection, hydrostatic test pressure MPa, during hydrostatic testing, water pressure should slow down. When the pressure rises to 0.1MPa, the water pressure should be increased to 0.1MPa. When the ambient temperature is higher than 5C, hydrostatic test should be carried out; when the temperature is lower than 5, should be protected from freezing water pressure test. Hydrostatic test water is generally 20-70.6, should be as light fuel oil or gas oil (China) as the fuel, the fuel oil is generally heated to 100 deg.] C, a viscosity less 30E. Oil Qbw = 10200Kcal / kg LHV viscosity of the oil is lower than at 50 ℃ 200E, at less than about 80 ℃ 200E, 50e is less than the heat value of natural gas Qbw = 8550Kcal / kg LPG Qbw = 22000Kcal / kg.
The oil in the gas-fired boiler, it carries on the classification according to the partition, has what kind? How to avoid the problem of ash accumulation in boiler superheater? And, with regard to boiler this important website product, what other questions need to be explained and answered? The main purpose of raising these questions is to solve them thoroughly so that we can understand them clearly and have a correct understanding.
01. What are the specific types of oil in a gas-fired boiler, if it is classified according to its formula? If oil in gas-fired boilers is classified by formula, then it can be divided into two categories: alcohol-based and petroleum-based. Moreover, alcohols are usually composed of methanol, or ethanol, and other high-carbon alcohols, while petroleum is a mixture of various waste oils and light oils, with a calorific value higher than that of alcohols. 2. How to avoid ash accumulation of boiler superheater? In order to avoid ash accumulation in boiler superheater, attention should be paid to the rationality of flue structure and the correct flow direction of flue gas when passing through the superheater. In addition, soot blowing can be carried out frequently, so that this problem can be avoided, and at the same time, ensure that the boiler can work smoothly and normally. 3. Lighting requirements for water and pressure gauges in gas-fired boilers and contents of boiler nameplates
20 years adhere to long and arduous, but parties were quick early heart never forget the moment, stick to date, the performance results are now almost 20 years trying to best each other gifts. Achieved remarkable results, the Group's own sound inseparable, inseparable from distributors around the trust and support. In the new market competition, will quickly adapt to the times square in the flow, leading the development of the Group through concerted efforts of all my colleagues and friends dealers, tenacious struggle, the successful realization of the new grand blueprint!
Steam boiler is too many forms, take an ordinary fast-packed 4-ton steam boiler. Water is heated into steam in the drum and heat is emitted by fire in the furnace, which is the principle of the steam boiler. Say the boiler first the pot. The boiler is a drum boiler with water cooling. Two return pyrotechnic tubes are arranged in the left and right parts of the drum, and the front cigarette box in the front part of the drum is turned back. Between the drum and the bottom box, there is a drop tube and a water-cooled tube, forming the frame of the combustion chamber. There is a steam separator on the top of the drum to reduce the water produced by steam. The heating surface of the boiler is the lower part of the drum, water-cooled pipe and pyrotechnic pipe. The combustion part consists of a chain grate and a drive device, Add the boiler frame on the grate of the composition of the combustion chamber composition. Surrounded by refractories. Coal from coal hopper, there are coal gate to control the thickness of coal seam while sealing the front of the air. The lower part of the combustion chamber is the place where the blast enters, and this kind of boiler has great resistance and needs forced blast. Cinder, discharged from the back of the grate through hawk iron and sent out of the furnace by the slag extractor. From the back of the boiler, the flue gas goes forward from the first return pipe of the boiler, the second return pipe returns to the rear part of the boiler, and then goes into the dust collector to separate the ash, and then through the draught fan, it is discharged from the chimney. The induced draft fan is not only the exhaust gas, but also necessary for the negative pressure operation of the boiler. Steam boiler is pressure capacity Device, safety device is necessary. Essential water level gauges, pressure gauges, safety valves, thermometers, electric pumps that can replenish water under pressure, and steam pumps that can also be used in the event of power outages. Boiler water must be softened and water treatment equipment.Free Chat
Copyright © 2020.Company name All rights reserved.