Steam 1000kg h diesel boiler pressure gauge and hydraulic accumulator Henan fast boiler's steam boiler introduce small series with a pressure gauge and hydraulic accumulator steam boiler pressure gauge should pay attention to: 1, rated steam pressure of less than 2.45MPa steam boiler , not only the accuracy of the pressure gauge to 2.5; rated steam pressure 2.45MPa promoter or equal to a boiler, the pressure is too spread made not less than 1.5. Dial gauge diameter of not less than 100mm, in order to ensure the operation of the operator to see the surface of the pressure value shown. 2, should draw the red line on the dial gauge steam boiler, he pointed out that the maximum allowable working pressure. 3, the steam boiler pressure gauge should be provided at a convenient place to observe and purging, and to prevent the high temperature affected, freezing and vibration. 4, steam boiler pressure gauge should check at least every six months once the check should seal. 5, the pressure gauge connection tube steam boiler should leaks steam leakage phenomenon, otherwise it will reduce the pressure instruction value. 6, a steam boiler gauge scale element should be compatible with the measured working pressure, the working pressure is usually 1.5-3 times, preferably 2 times. When no steam boiler gauges, pressure gauges or pressure damage did not meet the requirements of the apparatus, boiler steam pressure gauges of the following circumstances, should stop using: 1, the surface glass breaking or blurred dial scale; 2, no seals , damage or seal verification period exceeded; 3, no pressure gauge pointer finite bit staple staple can not be restored to the limit at infinite set of bits from zero gauge pressure exceeds the pressure data bits garment allowable difference?; 4, the jump table or a pointer leak; 5, other effects gauge accurate defect. The use of the accumulator: the accumulator for a hydraulic accumulator system intermittent mechanical, hydraulic fluid may be stored in the actuator output when a batch or a low speed, and the actuator requires a large flow of fast-moving, as an auxiliary energy providing oil to the system together with the hydraulic pump, oil pump and thereby achieve miniaturization of the entire hydraulic system, to achieve the object of absorbing the impact energy sudden change fast opening and closing valve and the hydraulic load, the system generates a pressure shock, pet cause vibrations and noise, and even damage the machine. The accumulator can be alleviated, which absorb fluid shock absorber pressure pulsation absorbing accumulator, and reducing the pressure pulsation and flow pulsations of various pump, thereby reducing system noise and vibration. Having a damping effect of the gas spring accumulator, it can be used to absorb the mechanical vibrations between the body and the traveling wheel of the vehicle and the like. The accumulator can be balanced upright actuator (hydraulic cylinder) and gravity load decreases when the potential absorption into hydraulic energy store, while generating the rate-limiting resistance; upright when the actuator rises, releasing the original absorbing energy accumulator , together with the pump oil to the hydraulic cylinder, in order to achieve balance and energy.
Steam 1000kg h diesel boilers and thermal oil heaters which is better? Which is more energy-efficient? Steam boilers and thermal oil heaters, which is more fuel cost savings? At the same power (represented with evaporation) for comparing the boiler, HTF medium because of the high temperature, so that the temperature of the steam exhaust gas temperature than the exhaust gas with a higher heating power of the boiler, the exhaust gas temperature directly affects Thermal efficiency. That same power (represented with evaporation) conditions, the efficiency is not high efficiency oil boiler steam boiler. In fact, now you finally choose what kind of boiler is required to rely on the temperature of your decision. If you ask a medium temperature to 300 degrees, you can only choose oil furnace; if you think there is a live medium temperature of 180 degrees is enough to use, it is recommended that you choose a steam boiler, because it is more energy-efficient with conditions). These are the kind of steam boilers and thermal oil heaters and today we analyze all the information of more energy-efficient, and the above information indicates that the steam boiler more energy saving, more fuel-efficient.
In October 2016, my company and the China Dunhuang International Hotel signed a ZWNSL2.1-1.0 / W-Y.Q vacuum condensing gas hot water 1000kg h diesel boiler to provide heating and hot water for the hotel. The boiler implementing the response to the national policy of environmental protection requirements and local environmental protection departments on a series of low nitrogen emission standard boiler requirements, in terms of design, manufacture, installation and other sectors have strict checks to ensure that the boiler safe and stable operation.
Gas and compare the economic performance of natural gas and oil-fired 1000kg h diesel boiler desulfurization: gas boiler for this kind of boiler, I believe we are not unfamiliar with it, because the site has its relevant articles, so that we know and understand this kind of boiler, and At the same time, you can give yourself a good learning quality and effectiveness. Below that, since there is already a foundation, we might build on the progress to continue this work so that we can deepen their understanding of the gas boiler. 1. The oil and gas boilers, in which economic performance is better? This problem, if from a professional point of view, then, there is no standard answer, because they can not determine. Related factors, mainly to see the area where the boiler and fuel is cheap or cheaper gas. In addition, the need for computing work, so in order to obtain accurate results. 2. Gas boiler gas consumption, and whether the type of gas related? In addition, the home heating system, the boiler is circulated to what? Gas consumption gas boiler, which is related to the type of gas, so in a question on which the answer is yes. Also, the heat value of natural gas, is 8500 kcal / cubic. While the calculation formula is 1.5 million kcal / 8500 kcal = 176 cubic meters. Other gas is so. Home heating system, if using gas boilers, then, that in the cycle, generally speaking, is to use the pump, because it is more appropriate, and that is a good use of effects.Free Chat
Copyright © 2020.Company name All rights reserved.