Classification and characteristics of oil-fired boiler which when the weather gets colder, people will choose different heating methods, which have a more convenient way is oil-fired boiler, but many people do not understand his usefulness, then together below take a look. Category: oil-fired boiler is the practical use of fuel, the boiler various boiler with diesel fuel and waste oil, his overall construction and arrangement of the gas boiler is similar to a common classification of mechanical and steam materialized style. Features: Multi-Fuel bottom of the pot is made of the holding furnace bottom is inclined to the back wall for holding furnace bottom, in order to obtain good combustion characteristics. This is not the kind of boiler for the gas pipeline, also want to be able to lower the cost of the normal operation of the boiler, then oil-fired boiler is a good choice. Oil-fired boiler is an important sign of progress now era, the purpose is to serve humanity well, according to further improve the people's needs.
Gas boiler cook stove Note: As the boiler equipment kinetic energy sources in the manufacturing, transportation, installation and maintenance process will bring oil and other impurities, persist in the boiler, it will not only clog water pipes, deteriorating the quality of steam, but also will reduce the heat transfer effect, the heating surface prone to overheating cause burn. Therefore, for removing impurities boiling out this step, the stable operation of the boiler is an integral part.
ASME is referred to as "the American Society of Mechanical Engineers", mainly dedicated to the development of machinery industry standards, and was recognized by most countries in the world. Get ASME certification is fast boiler and pressure vessel products to the international market, the only way to obtain a certificate issued by ASME and stamp means getting the products exported to international market, "pass."
Recently, many users of the phone does not know how to shutdown after the 14 tph capacity fired steam boiler maintenance, boiler maintenance is very simple in fact, today we explain the steam boiler and hot water boiler shutdown after: After the steam boiler maintenance shutdown method how maintenance. Since the cause of boiler failure or power shutdown required boiler, a steam boiler before travel should stop combustion boiler, the boiler slowly lowering the temperature until no pressure boiler, should pump before shutdown, induced draft fan and turn off the blower. After the maintenance shutdown home for boiler, furnace divided into external corrosion and home for the pot. Pot corrosion enjoying, enjoying their home for two kinds of wet and dry selected based on the length of shutdown time. When long-term disabled boiler, furnace should be paid close attention to external corrosion problems take care of themselves. First, the boiler shutdown cooling is necessary as far as possible completely eliminate fouling and ash grate heating surface of the upper, the lower portion of the furnace. Then have to adhere to certain natural ventilation flue. Under normal conditions, should be placed to dry moisture-proof agent in the furnace, flue. The dry quicklime as used, the furnace or the flue gas per cubic meter of ordinary should be placed about 3kg. After placing all the ventilation should be tightly closed doors. Lime powder to change after change. Such as boiler rooms in low-lying position, the air during shutdown severe flood tide, the method should be used regularly and placed a small fire to dry dry agent phase separation. If the boiler boiler long time, in order to thoroughly clean the soot topcoat red lead oil furnace or other metal surfaces in the anti-corrosion paint. As for the way home for corrosion inside the furnace shutdown, the shutdown Yaoan the length of time to be. Under normal circumstances, no more than one month shutdown of the available wet home for a month or more should take care of themselves dry. Dry to pay attention when enjoying the following questions: Do not dry agent in direct contact with the metal outer boiler, can be housed in a container such as an iron plate; dry agent after standing, for shutting the hole and the other hand hole cover, the vapor, the water pipe necessary to cut off valve; variant lime powder should be replaced. While enjoying wet, to pay attention to boiler water condensate is preferably used, followed by the available existing boiler water, demineralized water again; after adding the base, with a slow fire boiler water is heated to 80 [deg.] C to 100 the pressure rose to 0.2 maintenance after 0.3MPa 2 to 3 hours, so that it reaches the furnace circulating water alkalinity balance, pressure is reduced, then fill the boiler water, a certain gauge, and continue to adhere to this pressure throughout the home for alkalinity should be regularly tests, decreases should be added at any time; in winter, wet enjoying pay attention to antifreeze, especially the local sewage channel and economizer; before re-use should release all the pot boiler lye, best prepared sump, in order to facilitate further use. At the same time should be rinsed with clean water. The performance characteristics of coal, oil, gas steam boilerFree Chat
Copyright © 2020.Company name All rights reserved.