The advantages of gas 15 th steam boiler which is now very popular gas steam boilers, and many other types of boilers are selected by the user to be the transformation of gas boilers gas boilers, the advantages of gas steam boiler, what does? Today small breakdown of the gas for you What are the advantages of a steam boiler. First, let's take a look at the fuel gas fuel with respect to what other advantages: 1, good combustion process using readily mixed with air, exhaust loss of small, high-efficiency boiler; parts of sulfur and low ash fuel, heating surface coking does not occur and high temperature corrosion phenomena; high gas velocity, small overall size boilers, low boilers metal consumption; 2, adjust the properties of flexible gas heating value is easy to adjust, both fuels blending can be used; the same is applicable to multi-boiler such fuel; has a strong ability to adapt to changes in the heat load, the combustion easily achieved adjustment; 3, environmental pollution not directly broken, quieter operation case; ash and sulfur content is much lower than that of coal and oil fuel; when the burned gas is not ash generated when a large amount of gas to be treated; small contamination of soil; low dust content in the flue gas, a small air pollution; oxynitride main pollutants produced during combustion; 4, main pipeline transportation easy transport, no transport vehicle during Feisa, noise pollution; use, no gas as required before crushing. These are the advantages of gas fuel, in fact, the advantages of gas fuel can also be seen as the advantages of gas steam boiler. Here, the advantages of gas steam boiler, what does the first, gas boiler ash pile is not required to save the land;? Second, saving water boiler auxiliary production. Gas boilers and gas water boiler is equal to the normal production, but saves the auxiliary gas boiler for water gas boiler dust, slag and other dust, while not need to configure an accessory device and a fuel drying apparatus slag or the like can be greatly reduced boiler the investment costs; third, reduce staff, saving labor costs. Gas boiler auxiliary boiler equipment less than gas, fewer staffing requirements, the burden of wages and benefits would cost much less. While reducing labor intensity, gas boilers in coal transport, slag process requires high physical strength, and gas-fired boilers staff labor intensity is small; fourth, saving the cost of production of electricity boiler. Less gas boiler fuel delivery and other auxiliary equipment, low-power, continuous running time is short, so low power consumption, compared with the cost of the province; fifth, gas boiler room layout flexibility, small footprint, low noise generated; sixth, Improve the environment. Generate a lot of smoke gas boiler is running, causing great pollution cleaner, gas boiler environmental protection of the environment, due to the ash content of the gas, sulfur and nitrogen volume is lower than the content of the coal, flue gas dust generated by combustion minimal, flue gas emissions is easier to reach national standards required for combustion equipment, can greatly reduce the pollution of the environment.
A, WNS series automatic fuel (gas) 15 th steam boiler 1, an internal combustion boiler using a horizontal double quick return smoke wet back structure, the body-mounted using the waveform furnace, combustion chamber and back to the waveform furnace, connected to threaded pipe. After exotherm temperature flue gas flame in the furnace, carried to the threaded pipe via the folded back to the combustion chamber to the convection heat before entering the smoke chamber; high temperature flue gas enters the condenser back energy, the heat transfer by sufficiently by chimney into the atmosphere. 2, for a variety of boiler fuel oil, natural gas fuel, city gas or liquefied petroleum gas. 3, the boiler before the smoke box with movable lid cigarette, demolition, convenient rear access. Boiler with integrated burner, has started fast, high efficiency, high degree of automation features, the need to provide for a variety of local life, civil and industrial steam. 4, a boiler with full instrumentation system valve, the valve body has a boiler inlet valve, check valve, the main steam valve, safety valve, drain valve, air valve and the combustor brought solenoid valve. Water meter with a measuring point pressure display, display and control drum pressure, exhaust gas temperature display, the temperature and pressure of the burner is displayed. 5, combustion and boiler feed water using automatic control, automatic adjustment, easy operation, low labor intensity and safe and reliable protection devices, easy maintenance and repair.
Combustion gas treatment unit and a fault, gas boiler burner ignition misfire rod reasons: 1, the ignition bar gap interposed carbon residue with oil. 2, ignition rods fragmentation. moist. Leakage. 3, the distance between the ignition does not stick, too long or short. 4, ignition rods Insulation damage, short to ground. 5, ignition cable and transformer failure: cable, connector damage caused by a short circuit during ignition; transformer break or other fault occurs. Measures following five: Clear, renewal, adjust the distance, change and switching transformer. Second, gas boiler, but spark ignition rods misfire reasons: 1, the cyclone disc space ventilation is blocked carbon, poor ventilation. 2, dirty oil nozzle clogging or wear. 3, the throttle angle is set too small. 4, the firing bar from the leading edge from the oil nozzle tip inappropriate (too protruding or retracted) 5, the first solenoid valve is an oil debris blocking gun (gun small kerosene). 6, oily or too viscous to flow easily clogged or the oil filtration system the valve is not opened, so that insufficient suction pump, oil pressure. 7, the filter pump itself blocked. 8, the oil more water (boiling abnormal noise within the heater). Measures are: Clear; first wash, such as not renewed; turndown test; adjusting the distance (in 3 ~ 4mm as well); Remove cleaning (cleaning the parts diesel); Check tubing and oil filters, insulation equipment ; remove peripheral screw pump, carefully remove the cover inside out oil network, with immersion oil; renewal of the test oil. Third, when the gas boiler and turn the fire a small fire normal, off, or flashing instability reasons: 1, the air volume damper setting fire too. 2, oil fires micro switch valve (damper outermost that group) inappropriate setting (set throttle air flow rate is greater than the fire). 3, oleaginous easy to spray viscosity is too high (heavy). 4, and the nozzle plate spacing cyclone inappropriate. 5, fire nozzle worn or dirty. 6, the preliminary fuel tank temperature is too high, so that the steam not smooth oil pump oil feed. 7, fuel oil boiler water. Action: Test gradually reduced; heating temperature; adjusting the distance (between 0 ~ 10mm); clean or replace; approximately set to about 50 deg.] C; or drain oil change. Fourth, the noise increases gas boiler burner reasons: 1, cut-off valve is closed or the passage into the fuel shortage, an oil filter blockage. 2, the oil inlet temperature is low, the oil viscosity is too high or the temperature is too high the pump inlet. 3, oil pump failure. 4, fan motor bearing damage. 5, dirty fan impeller. Processing methods: ① the oil line check valve is open, if the oil filter is working properly, the filter cleaning pump itself. ② heating oil or reduce the oil temperature. ③ Replace the oil pump. ④ replace motor or bearings. ⑤ cleaning fan wheel.
We produce 15 th steam boiler is a very important part of the device, this provides a quick way to our gas steam boiler, after use, we found an excellent energy-saving effect boilers, flue gas discharge temperature is lower than the previous boiler equipment many, in line with national environmental provisions of the boiler equipment. --customer feedbackFree Chat
Copyright © 2020.Company name All rights reserved.