Note the choice of industrial boilers from the first industrial revolution to develop microbial technology, and upgrading various products continue to emerge, led us to the development of human civilization from the original backward to technological civilization, to the boiler, for example, since the last century, there has been a cylinder since the boiler-shaped, with the needs of science and technology and production, from simple to complex, from single to serialization, boiler technology are developing rapidly, the good reputation of industrial boilers companies choose to share precautions industrial boilers; first, the coal use; the design of the cell structure based on coal boiler components as the design basis, select the boiler should pay attention to adjust to the type of coal in the region. It recommended new, high-efficiency, high-tech, high-quality, durable industrial boilers; second, parameter selection; industrial efficiency boiler work normally when approaching the highest efficiency rating, as the load decreases efficiency has declined. Boiler capacity is generally selected: it generates a large steam than the actual gas consumption, such as the required parameters and actual parameters difficult to match industrial boilers, high boilers in this case a gear selection parameter. Selection of auxiliary boiler should also refer to the above principles, to avoid the "big horse car"; third, the number of choices; normal maintenance of industrial boilers and boiler shutdown is a number of factors, but also pay attention to: the boiler room shall not exceed the number of boiler economizers work load, install boiler economizer device purpose is to avoid too much heat when the smoke away. Improve the thermal efficiency of the boiler, is provided in the back pass boiler economizer heating surfaces, the use of flue gas heating boiler feed water, to save energy, economizer after the installation, the boiler increases the thermal energy required for heating the feedwater, boiler water and so reducing the temperature difference between the water supply, reduce the burden of heating boiler feed water. Cause excessive number of boiler economizer can not play a role, resulting in waste of energy; These are high-quality industrial boiler company to share some notes selected industrial boilers; vast land of our country, many places are rich in coal, resulting in different types of coal , which has also become a basis for selection of parameters and select the number of boilers enable us to be more effective in energy conservation, to achieve a win-win.
Provide for the growers Kingenta Ecological Engineering Group, the main compound fertilizer, slow release fertilizer, water soluble fertilizer, bio-fertilizer, soil conditioner, etc. required for a full line of soil and - with another giant fertilizer industry enterprises farming solutions services. 2016, Kim Jong large group with my company, to buy one of two 10 tons of steam condensing 200kg hr diesel steam boiler (WNS10-1.25-Y.Q). It is the product side were quick constant pursuit of quality, in-depth research and development of control and intelligent control, boiler energy efficiency as well as high demand for continuous improvement of energy efficiency and emissions, making the fertilizer industry's two leading companies invariably choose the fast way hand in hand!
Tail gas boiler heating surface, promote energy conservation, 200kg hr diesel steam boiler, make full use of surplus gas, iron and steel ring can be part of the No. 2 boiler recently implemented gas utilization upgrading the premise of low temperature corrosion does not occur. The transformation of the original two No. 2 Power Station Boiler 220 t / h circulating fluidized bed boiler, the transformation of 200 tons / hour gas-fired boiler. To reduce the cost, Shaoguan Iron & Steel ring portion can be modified in the original boiler equipment, removal coal system, discharging systems, dust removal systems, fuel systems; Lee used equipment including the original boiler water wall, drum, steel frame, platform escalators, tail shaft convection heating surface, steam systems, water systems and some electrical, instrumentation and other facilities, while adding the blast furnace, a coke oven gas in each system, the new blast furnace, coke oven gas mixing burner 4, the combustion of blast furnace gas device 4, a low-low pressure economizer, the boiler flue gas boiler guaranteed emissions compliance and four 10 kV high-pressure fan, part of the electrical and gas drainage, tail heating surface is not provided at a low temperature corrosion occurs meter facilities. No. 2 boiler after the upgrade, to ensure the boiler flue gas emissions standards and low temperature corrosion tail heating surface does not occur under the premise, as far as possible be able to mix more burning oven gas, surplus gas consumption, save energy and reduce environmental pollution.
Gas boiler heat loss through the combustion of fuel gas boiler, will release some heat, which will supply part of the user, some will be recycled and part is inadvertently wasted. So these are wasted heat lost through the ways in which it (1) heat losses:? Flue gas exhaust gas boiler part of the heat into the atmosphere, causing the boiler heat losses, it is each boiler term heat loss Dazhong biggest one. The main factors influencing the heat loss is higher exhaust gas temperature and the amount of smoke exhaust gas temperature, the greater the amount of smoke, the greater the heat loss. Low exhaust gas temperature depends mainly on the number and operating conditions of the heating surface; the amount depends on how much leakage exhaust case and the furnace excess air, flue. (2) heat loss incomplete combustion gas: a part of the unburned combustible gas is discharged with the flue gas to heat loss caused by heat in the flue gas. The main factors affecting the incomplete combustion gas heat loss is the excess air and furnace structure. Excess air coefficient is too small, uneven air is mixed with fuel, easy to generate carbon monoxide and other combustible gases; excess air coefficient is too large, the furnace temperature is lowered, the combustible gas is not easy ignition and combustion. Furnace volume is too small, combustible gases in the furnace too late to enter the combustion flue gases caused by incomplete combustion heat loss. (3) heat loss: the furnace heat loss, frameworks, pipes, door opening caused by heat dissipation to the surroundings. Size depends on the heat loss factors of the size of the surface area of the furnace gas 200kg hr diesel steam boiler, heat insulating properties and thickness, the outside air temperature and the flow velocity. Electric heating reactor common external damage: an electrically heated reactor despite external corrosion has a high etching resistance against acid and alkali resistance, but our electrical heating by the heating apparatus is a kettle layer and an outer tire iron constituted. Such a medium is iron acids and bases are not corrosion-resistant. If we would have the production process if the reactor cover or screwed pipe joints without seal failure or leak acid tire iron reactor apparatus for electrically heating the outer corrosion. Corrosion support member 2. The reactor was heated electrically heated reactor during installation, support or other support member may be mounted directly on the floor, due to the long manufacturing operations on the floor may be deposited with corrosive media, so that for support our reactor electrically heated apparatus corrosion, resulting in the supporting force of each of the support produces a change resulting in a change in stress in the damage produced during heating layer. 3. The electrically heated reactor stress spout in the electrically heated reactor, when the steel of the pipe and the pipe joint, since the thermal deformation and the reaction was heated electrically heated autoclave vessel or duct stressed cold might damage the pipe.Free Chat
Copyright © 2020.Company name All rights reserved.