Our emphasis on increasing green, local governments also boiler operation produces nitrogen oxides and smoke emission requirements become more stringent. Fast boiler followed by the national trend of development, deepening of cleaning boiler product design and development. Lulu as a representative of business development of the national beverage, and hope to find a set of boiler energy conservation and clean in one, for drink production process of fermentation, sterilization, drying, curing and other processes. After many visits and market research, in October 2017 and entered into boiler fast boiler purchase contracts, purchase two 10 tons of steam and a whole 20 tons of steam condensing 300kgh steam boilers. The two sides this cooperation is the other quality fast condensing gas boiler highly recognized, has proved a powerful strength fast boiler in the boiler production and service of gas condensate from the side.
Steam Gas Gas Desulfurization to achieve excellent results steam oven gas steam oven must sample tests, the thermal conductivity was measured quality of appearance, flash point, viscosity, acid, water, and carbon residue, provided with heat transfer fluids plant proof mass It is consistent with the book, but also provide the basis for future changes in the operation of medium quality monitoring. Means passing the tests of the gas-steam heat transfer fluids using pumps to transfer fluids within the furnace and the injection of hot expander. When pumps heat transfer fluid to the injection system, should check again the furnace, heating equipment, piping system drain valve, drain valve is closed, in order to avoid loss of heat transfer fluids. While the exhaust pipe and the valve opening on the furnace one by one, to exclude air, until a closed gas steam flows. It stops when the oil level gauge appears on the expander injection heat transfer fluids, and then start the circulation pump, for circulating cold. Existing gas steam oven dry dust, do not meet wet desulphurization process of flue gas CWS humidity, water vapor in the flue gas as coal-water slurry up to 36%, some as high as 40% or more water content of coal-water slurry, If we consider only the dust and sulfur dioxide that is not enough. Arts gas 300kgh steam boilers company after multi-party experts to study, test, develop a dusting product, the successful use of coal-water slurry plenty of water in the flue gas as a carrier, by cooling, reducing condensation, dust and sulfur dioxide capture down, to achieve excellent results gas desulfurization steam oven. The effect of dust reaching the user's satisfaction. Gas welding gas steam oven must be operated by welders holding boiler and pressure vessel certification of welders. Welding dimensions meet the design drawings and process documents, bead height is not less than the base material, the base material with a smooth transition. Gas fuel gas steam oven weld and heat affected zone no cracks, holes, craters and slag. Weld undercut hole deeper than 0.5mm, the total length (the sum of both) is not more than 1/4 of the circumference of the tube, and not more than 40mm. Construction of gas steam oven strict compliance with welding procedures and other relevant standards and regulations, and make construction records welded to record the record.
How to improve the thermal efficiency of gas 300kgh steam boilers steam boiler to improve the thermal efficiency of gas is a problem many users are taken, I believe this issue is the direction of each used in the production of various types of gas steam boiler manufacturers have been in the study. Many users at the time of the gas-steam oven operates, often in the actual production process, we found some new problems, but all the problems, the most vexing is the high temperature exhaust gas steam boilers, thermal efficiency than low phenomenon that a serious impact on our work, then how should we do to improve the thermal efficiency of it? need to know this is the best way to meet the low-temperature properties of gas and steam comes as synthetic gas steam. However, the vast majority of synthetic gas and steam biphenyls, benzene derivatives of both components of the complex, or a vapor of volatiles has strong carcinogenicity, it is strongly recommended that the client select the type of mineral oil vapor product gas. Second, gas and steam products to meet the low temperature performance process, but also have a relatively high flash point required. In general, gas steam engineers suggest, low temperature gas steam flash point not lower than the opening 200 ℃. After a professional manufacturer of continuous research and improvement of its equipment, in order to improve its thermal efficiency was found to be increased tail gas steam boiler heating surface of, say, air preheater and economizer. But when organic heat carrier furnace return temperature is high, you can not set the economizer, air preheater can only be set to alleviate the situation. So if no gas steam boiler and other heating systems for low temperature heat exchanger, then the only way to improve the energy efficiency is adding air preheater. After adding air preheater can be a corresponding increase in gas flow rate of steam, gas steam boiler in order to ensure safe, reliable and stable work, the thermal efficiency of gas-steam boiler plant will be a corresponding with the increase.
Check the work before the start fuel gas-fired boiler in order to protect the safe operation of the gas boiler, improve operational efficiency boiler, make sure to check the work before the boiler starts, every detail can not be ignored. 1, check the safety accessories, thermal instrumentation, electrical instrument should be intact; 2, check the connections, whether the water leakage and the furnace body line; 3, check the waste line, the water line, return line should be smooth; 4 , should check the line voltage is 380V, the fluctuation should be within ± 5%; 5, oil-fired boiler and a filter pump check whether normal oil, gas boiler check the gas pressure is normal, not too high or too low, the oil supply opening valves; 6, check whether the pump Sheung Shui, or opening the purge valve, until the Sheung Shui so far. Water Supply System opens each valve (including the water pump and water valve before and after the boiler); 7, check level gauge, the water level should be in the normal position, to prevent false water level, if the water can be manually Sheung; 8, check the pressure conduit the valve must be opened, the wind deflector must all flue opening; 9, each knob inspection control cabinet are in their normal position; 10, a check valve should be 300kgh steam boilers in a closed state, the hot water boiler circulating pump valves should be closed state; 11, check water softening equipment is operating correctly, create a variety of indicators of soft water meets national standards. Carefully do the above inspection, the basic conditions for the fuel gas boiler safe and economic operation.Free Chat
Copyright © 2020.Company name All rights reserved.