State all the more attention to environmental protection, to provide more excellent atmosphere, we respond positively to the country's environmental protection, promote the 50 tons fired boiler from coal to gas project. Among the many boiler suppliers, we chose the fast boiler. First, the party quickly done very well in terms of cleaning the boiler, the second is fast side also very comprehensive after-sales involved. The optional gas boiler was used after running fully meet the needs of our pharmaceutical production, both energy-saving and environmental protection, but also a very high thermal efficiency, saved us a lot of fuel costs. --customer feedback
Reform technology of coal-fired 50 tons fired boiler combustion mode retrofit of coal-fired boiler by means of this technology, proper pulverized coal can be injected into the proper position of furnace chamber, and appropriate suspended combustion can be added on the basis of furnace row layer combustion, which can achieve a certain energy saving rate. For fuel oil and gas-fired boilers, the old and backward burners can be replaced by new energy-saving burners.
Further, out of the boiler removal methods include eliminated, an alternative centralized heating boiler, coal gas, coal to electricity, use geothermal, wind, solar, biomass with baghouse, clean coal to burn not including , CWS, anthracite, semi-coke, green coke, crude oil, coal-fired boiler removal must be removed chimney or flue physical cutting, it does not have the complex production conditions. Do not use has been shut down, eliminated waste coal-fired boilers to cash rewards and subsidies. In the process of new coal-fired boilers to switch to natural gas to be synchronized to achieve low nitrogen transformation.
The reason the gas 50 tons fired boiler burner increased noise analysis when making use of the gas boiler and found this small fire normal, but this time turn the fire, extinguished or flashing instability. First speaking, that is because of this fire damper of the air volume setting is too large; i.e. after an oil fire because the micro-switch valve (damper outermost that group) inappropriate setting (set lower than the fire damper of the air flow larger) burner gas noise increases, mostly because the oil shut-off valve which is closed or lack of oil into the oil filter clogging; or, this is because of low temperature into the oil, the viscosity is too high or the pump into the oil temperature is too high; oil pump failure; fan motor bearing damage; there is because the fan impeller dirty equipment resulting in large noise. The above-described failure when using gas boiler, but also because the viscosity is too high oleaginous easy to be atomized (heavy oil); cyclones and because improper disc and the nozzle pitch; Note that because the fire is worn or dirty nipple; also because this preparatory tank the heating temperature is too high, causing the oil pump oil feed steam does not conform; or because the fuel inside the boiler resulting aqueous oil. When the above-described fault gas boiler used to perform this process, the test should be done gradually decreases; after heating temperature should be; adjusting the distance (between 0 ~ 10mm); clean or replace; is set to about 50 deg.] C to about; or drain oil change.Free Chat
Copyright © 2020.Company name All rights reserved.