Gas oil furnace gauge acceptance and prohibit the use of instructions for conducting oil furnace oil furnace gas this kind, since both sites 5000 kg small fired boiler products, is one of the sites keywords, therefore, requires a comprehensive knowledge and understanding. Moreover, it is also a common oil furnace type. Therefore, only familiar with this kind of boiler, we have the right to use, so a lot of benefit to themselves. 1. Gas oil furnace acceptance for this kind of a gas oil furnace oil furnace, which work in the acceptance, the main, are: First, when a gas oil furnace transported to the installation site, the manufacturer should be based on factory inventory, an inventory of its parts, whether there are missing and so on. Then, according to the boiler drawings, review of equipment, mainly to check its associated integrity. For example, the large boiler, during transportation, whether there is damage or deformation such problems. 2. Gas oil furnace gas pipeline for oil furnace installation, in which the pipeline installation, requirements mainly refer to "Heat Transfer Fluid heaters Safety Supervision" in, and should refer to product specifications, as well as the process of FIG. to carry out. For the line connection port, in addition to the flange on the connection should be used to this kind of welding. In addition, the pipeline arrangement, there should be a slope, typically from 2% to 3%. In the high line, an exhaust port shall be provided, at its low due outfall. For straight line pipe, if the length is more than 20m, then there should be a thermal expansion joint. 3. conducting oil furnace gas gauge, when the circumstances under which can not be used? In the gas oil furnace, pressure gauge is an important instrument, but if some situation, then can not continue to use its specific terms, it is as follows: Case 1: broken glass on the pressure gauge, or its dial scale is unclear, unrecognizable. Case 2: Pressure gauge seal is damaged, or it exceeds the test period. Three cases: for a limited gauge nail stop, if there is no pressure, the pointer can not limiting, the staple at the back. If the nail is not limiting, pressure gauge, in the absence of pressure, which is the distance between the pointer and the zero position, more than a predetermined allowable error range.
What is "green 5000 kg small fired boiler" "boiler environmental protection" is a more general concept, a broad sense, refers to the boiler exhaust emissions, waste emissions and other environmental requirements of the load does not refer to a certain kind of single boiler. According to China's latest introduction of emission standards of air pollutants in some areas, Beijing, Zhengzhou, Xi'an and other cities of nitrogen oxide emissions have been reduced to the minimum standard of 30 mg / cubic meter. For fuel gas boiler, the combustion by the use of advanced technology or environmental burner configuration to achieve NOx emissions below 30 mg / m, belong to "green boiler." Electric boiler not to detail that the use of electricity as power and energy, waste no exhaust emissions, but are "environmentally friendly boiler" type. Environmental protection boiler they use FGR, premix combustion technology and other advanced reprocessing of flue gas, the flue gas heat reuse, reduce exhaust gas temperature. Can improve the thermal efficiency of the boiler, and reduce harmful substances in flue gas emissions, energy conservation and environmental protection to achieve social, economic double benefit. Fast boiler cleaning has many years of experience in manufacture and sale of boilers, and has developed a number of patented technology, production of boilers meet the most stringent air pollution emission standards in China. If you have to "green boiler 'needs or problems, can contact me directly, professional and technical engineers in real time to answer your questions.
How to improve the thermal oil 5000 kg small fired boiler efficiency oil boiler thermal efficiency is a lot of users are taken into account, we believe that this issue is the direction of each used in the production of various types of oil boiler manufacturers have been in the study. Many users at the time of the oil furnace to operate, often in the actual production process, we found some new problems, but all the problems, the headache is higher oil boiler flue gas temperature, low thermal efficiency the phenomenon that a serious impact on our work, then how should we do to improve the thermal efficiency of it? need to understand this is to meet the low-temperature characteristics of the thermal oil comes as synthetic heat transfer oil. However, the vast majority of synthetic HTF complex biphenyls, benzene derivatives of both components, or a vapor of volatiles has strong carcinogenicity, it is strongly recommended to select customers conducting oil mineral oil products. Second, conducting oil products to meet the low temperature performance process, but also have a relatively high flash point required. In general, oil engineers suggest, low flash point not lower than the HTF opening 200 ℃. After a professional manufacturer of continuous research and improvement of its equipment, in order to improve its thermal efficiency was found to be increased oil boiler heating surface of the tail, say, air preheater and economizer. But when organic heat carrier furnace return temperature is high, you can not set the economizer, air preheater can only be set to alleviate the situation. So if the oil boiler and not other low-temperature heating system heat exchanger, then the only way to improve energy efficiency is adding air preheater. After adding air preheater can be a corresponding increase in the flow rate of heat-conducting oil, oil boiler in order to ensure safe, reliable and stable work, the thermal efficiency of the boiler plant with thermal oil will be a corresponding increase.
At the end of 2017, China Guodian is located in Jiangxi Province Wanan Hydropower Plant After evaluating the situation, some of the steam 5000 kg small fired boiler used to purchase much-needed daily work. Sales Manager fast boiler combined with the actual situation of the power plant for its recommendation 2 0.5 tons of electrically heated steam boilers.Free Chat
Copyright © 2020.Company name All rights reserved.