Gas-fired steam boilers are a very wide range of special equipments, widely used in food, chemical, paper, textile, construction and other industries. In the process of loading and installing a gas steam boiler, some problems must be paid attention, otherwise it may cause a certain degree of economic loss.
1. Pay attention to the following matters during the loading and unloading and handling of gas-fired boilers: the lifting capacity of the lifting equipment should match the weight of the lifting boiler. The lifting lug on the boiler with the lifting lugs that cannot be used for lifting can not be used for lifting. The length of the steel cord should be reasonably selected to avoid the scratching of the furnace due to the improper length of the steel cord. The boiler must be protected from any damage during handling and handling.
2. Reserves for maintenance space When installing boilers, ensure that there is sufficient maintenance space around the boiler.
3. Setting and precautions for the base and base of the gas steam boiler The boiler body must be installed on the basis of 100-150mm above the floor of the boiler room. It must be confirmed with the technical personnel of the boiler manufacturing company in advance and constructed according to the basic drawings. The anchor bolts must be reserved on the foundation. The foundation shall be capable of withstanding the maximum weight of the boiler and the amount of water it holds. When installing the base, you must first position it. After positioning, adjust to the same length of the two diagonals of the base, and then tighten all the fixing bolts. The installation of the base is carried out with reference to the reference line.
4, general precautions Be careful not to tilt and impact the boiler and accessories too much. No combustibles can be placed around the boiler. Do not use oil and water to smother the boiler. The boiler should normally be installed in a separate boiler room. The new gas-fired boiler room should not be connected to the house. The boiler room shall not be connected to Class A, Class B and Category C fire hazard rooms using flammable liquids. If connected to other production plants, the application firewall is separated.
5. The fire resistance grade and fire protection requirements of the boiler house building shall comply with the requirements of the Code for Fire Protection of Building Design and the Code for Fire Protection Design of High-rise Civil Buildings. The ground of the gas steam boiler room should be flat, non-flammable, no water accumulation, and the foundation load should meet the requirements. The power supply voltage of the gas steam boiler room should be stable to avoid causing the electrical components to burn out. If the voltage is unstable, it is recommended to install a voltage regulator. Ventilation equipment should be installed in the boiler room, and the boiler should be kept at room temperature below 50 °.
Recently, the Shuangyashan City, thoroughly implement the first meeting of the Central and the National Finance Committee, the province's environmental protection spirit of the General Assembly to further implement the "State Council on the issuance of winning the Battle of Blue Sky's three-year action plan" to do "atmosphere ten" task finishing verification and improve air quality living environment for the residents to protect the health of the people, combined with the actual situation, the specific "Shuangyashan City 2018 air pollution control implementation plan."
"Plan" focused on job content is to carry out comprehensive improvement of coal-fired boilers, effectively reduce coal pollution. Of built-up urban area shutdown, demolition, instead of using biomass fuel boiler inspection, investigation and comprehensive urban fringe areas built-up area if there is a new violation, missing, incomplete elimination of small coal-fired boilers, to eliminate incomplete, missing, "resurgence" boiler promptly dealt with severely, and formed out of work ledger, as planned phase-out. Existing "clear" action identified 28 small coal-fired boilers, before the end of September 2018, to phase out the "cleared" of work, and in strict accordance with the requirements "a furnace" during the establishment phase out the boiler archives for future reference. Planning the construction of central heating heat source, heat accelerate network construction and transformation progress, constantly expanding area of central heating and central heating ratio; advancing coal to gas, coal to electricity and other clean energy alternatives, to promote industrial parks and industrial clusters concentrated heat source, steam source facilities.
Battle of blue sky and started "out of coal-fired boilers" special action to start the county (district) level urban built-up area of 10 steam tons / hour and coal-fired boiler, tea furnace, operating coal-fired kitchen stove and other facilities, grain storage coal drying equipment out of work. County (district) to co-ordinate well out of work, organized a special team completed a comprehensive investigation of the status quo area coal-fired boilers, establish a list out of coal-fired boilers, the production out of specific programs, and to work out the boiler out of subsidies. Before the end of the first to eliminate a large number of pollution levels, residents reacted strongly to the coal-fired facilities.
Construction of gas 8ton cheap steam boiler in singapore steam requirements for the construction of a gas boiler requirements, gas steam boiler installation for the construction of the boiler room have certain requirements, must comply with national requirements in the construction process. Gas and steam 1, the construction of a gas steam boiler room requirements 1) boiler room must comply with the "boiler energy saving technical supervision and management regulations" and "industrial boiler room design specifications" requirement. Gas steam 2) boiler room should have sufficient light and good ventilation, have the necessary antifreeze measures. And boiler room should stay away from schools, housing and densely populated areas. 3) the position should be close to the boiler room heating equipment, in order to reduce head losses and heat loss from the hot oil piping circulating pump. 2, furnace heat carrier device is arranged in claim 1) the sump should be lower than the lowest position of the heat carrier furnace and heat system 1 m, in order to put the net organic heat boilers and systems, sump and furnace heat carrier spacing less than 5 m or separated by a partition wall. It should be fitted with a sump exhaust pipe, which exhaust pipe diameter should be large and specifications than the inflation tube. 2) position of the expansion tank should be higher than the other devices and the piping system, the system must be higher than the maximum bottom level 1.5 m. It should not be installed directly above any one boiler, organic heat carrier to prevent overflow cause a fire. 3) the sump vent pipe, expansion tank, should be connected to the outdoor safety. Can not be mounted on the vent pipe to the valve, to ensure that the tank, the expansion tank to atmosphere to ensure atmospheric pressure operation. 4) the high volume of the expansion tank should be greater than 1.3 times and all the organic heat carrier furnace heat the entire heating systems is at the operating temperature is increased due to thermal expansion of volume. 5) low volume tank furnace heat carrier to be less than 1.2 times the total amount of organic heat. 6) hot oil circulation pump should be at least four weeks for 0.5 m space, and the inspection to ensure the installation routine, the need for maintenance.
Recently, many users of the phone does not know how to shutdown after the 8ton cheap steam boiler in singapore maintenance, boiler maintenance is very simple in fact, today we explain the steam boiler and hot water boiler shutdown after: After the steam boiler maintenance shutdown method how maintenance. Since the cause of boiler failure or power shutdown required boiler, a steam boiler before travel should stop combustion boiler, the boiler slowly lowering the temperature until no pressure boiler, should pump before shutdown, induced draft fan and turn off the blower. After the maintenance shutdown home for boiler, furnace divided into external corrosion and home for the pot. Pot corrosion enjoying, enjoying their home for two kinds of wet and dry selected based on the length of shutdown time. When long-term disabled boiler, furnace should be paid close attention to external corrosion problems take care of themselves. First, the boiler shutdown cooling is necessary as far as possible completely eliminate fouling and ash grate heating surface of the upper, the lower portion of the furnace. Then have to adhere to certain natural ventilation flue. Under normal conditions, should be placed to dry moisture-proof agent in the furnace, flue. The dry quicklime as used, the furnace or the flue gas per cubic meter of ordinary should be placed about 3kg. After placing all the ventilation should be tightly closed doors. Lime powder to change after change. Such as boiler rooms in low-lying position, the air during shutdown severe flood tide, the method should be used regularly and placed a small fire to dry dry agent phase separation. If the boiler boiler long time, in order to thoroughly clean the soot topcoat red lead oil furnace or other metal surfaces in the anti-corrosion paint. As for the way home for corrosion inside the furnace shutdown, the shutdown Yaoan the length of time to be. Under normal circumstances, no more than one month shutdown of the available wet home for a month or more should take care of themselves dry. Dry to pay attention when enjoying the following questions: Do not dry agent in direct contact with the metal outer boiler, can be housed in a container such as an iron plate; dry agent after standing, for shutting the hole and the other hand hole cover, the vapor, the water pipe necessary to cut off valve; variant lime powder should be replaced. While enjoying wet, to pay attention to boiler water condensate is preferably used, followed by the available existing boiler water, demineralized water again; after adding the base, with a slow fire boiler water is heated to 80 [deg.] C to 100 the pressure rose to 0.2 maintenance after 0.3MPa 2 to 3 hours, so that it reaches the furnace circulating water alkalinity balance, pressure is reduced, then fill the boiler water, a certain gauge, and continue to adhere to this pressure throughout the home for alkalinity should be regularly tests, decreases should be added at any time; in winter, wet enjoying pay attention to antifreeze, especially the local sewage channel and economizer; before re-use should release all the pot boiler lye, best prepared sump, in order to facilitate further use. At the same time should be rinsed with clean water. The performance characteristics of coal, oil, gas steam boilerFree Chat
Copyright © 2020.Company name All rights reserved.