Gas Steam Boiler non-normal stall, a phenomenon and treatment, flame reasons: 1, the operation of the auxiliary power supply or trip interruption. 2, boiler combustion instability. 3, the load is too low, so that the load sharply mill automatic ignition energy loss or failure of combustion. 4, mutant coal, coal volatile or low calorific value. 5, the automatic combustion flame detector failure or failure caused by tripping mill. 6, or blast furnace wall tubes serious improper boiler soot-blowing operation, a large amount of water vapor into the combustion chamber. 7, coal pulverizing system, fuel system failure, resulting in a significant amount of fuel reduction or interruption. Or with a large amount of water in the fuel oil gun blocked too many impurities, low pressure steam or atomized. Second, the phenomenon: 1, a significant increase in furnace pressure, furnace flame monitoring flameless CRT display. See the fire no fire hole, BTG warning window MFT warning lights. 2, the unit load decrease, the steam flow drops rapidly, each segment working medium temperature, the vapor pressure decreases, the value of oxygen surge. Third, the method of treatment: 1, if the MFT tripping protection, should an emergency shutdown processing, stop the supply of fuel. 2, identify the cause flameout, and try to eliminate, to conduct a comprehensive inspection of the boiler, after confirming the device properly, can restart.
Chinese wine culture has a long history, wine blend. In the process of making wine, almost all wine prices are inseparable from the brewing process steam, we can say the stability and quality of steam purity of the wine production plays a decisive role. Lefort Wine has been committed to producing high-quality wine products, December 2016 No. 1, Lefort wine and I signed a one 4 tons of steam condensing steam boilers, the company continues to provide high-quality wine work steam.
Matters needing attention in installation of Gas-fired BoilerGas-fired boiler also says that gas-fired heating boiler is a kind of boiler which uses gas combustion to heat water to satisfy people's heating. It belongs to the category of domestic boiler. By gas-fired heating boiler we usually refer to gas-fired atmospheric hot automatic wns fired water boiler, gas including natural gas, liquefied gas, city gas, coke oven gas, biogas and so on. There are explosion-proof doors on the rear of the fuel-fired boiler or on the smoke pipe, and the position of the explosion-proof doors should be conducive to the discharge of the explosion. In cases where explosive gas may endanger the safety of operators, a pressure relief guide tube shall be installed on the explosion-proof door. The installation of boilers, auxiliary machines and water treatment equipment shall be in accordance with the technical requirements of the equipment manufacturing plant. . The equipment foundation must wait until the equipment arrives and checks correctly with the design drawing before construction. 3. When installing the equipment, avoid the equipment, and the installation material should be stacked on the floor. When using building column, beam lifting equipment, the bearing capacity of beam and column must be verified in advance. 4. After installation of oil, gas, hot water and steam pipes, the pressure test acceptance shall be carried out according to the Code for Construction and acceptance of Industrial Metal Piping Engineering GB 50235 / 1997.
Gas pressure hot automatic wns fired water boiler pressure introduction gas hot water boiler: gas pressure hot water boiler pressure vessel belongs, as always pressure hot water boiler is full of water, so no water level, but to be fitted with pressure gauges, safety valves and thermometers. Circulating pump pressure hot water boiler heating system is generally used in water pump, which is pumping systems engineering backwater sent to the boiler, it is necessary to overcome the resistance of the systemic circulation, but also to maintain a certain pressure boilers, hot water does not guarantee high temperature vaporization . Pressure hot water boiler can not only supply low-temperature water, but also to supply hot water Features: 1, boiler design, manufacturing, supervision and inspection are strictly according to "hot water boiler Safety Supervision" ensure long-term security and stability of the boilers. 2, the boiler body is a shell type three return all wet back downstream pyrotechnic pipe structure, large combustion flame in combustion chamber a slight positive pressure, combustion heat load is low, less NOx emissions of harmful substances. Through advanced machine test bed to test several times to verify the boiler under various load operation can get good thermal performance, qualified flue gas emissions targets as well as a wide range of burner adapter. 3, before and after the boiler smoke box with a special heat insulation materials, high temperature, low thermal conductivity, good anti-radical quenching heat capacity, greatly extending the life of the smoke box. A lower smoke box is provided with a condensate drain, water condensed reduce corrosion of the pressure receiving member. 4, the boiler and each pot spout means disposed reasonable to optimize the pot water circulation, prevent scale generation, but also help to improve the water side heat transfer. Set hand hole, inspection hole in the poor circulation of weak links, to facilitate regular inspection and maintenance. 5, the temperature of the boiler smoke box structure compared to dry wet back boiler back, greatly reduced, the smoke box solves the frequent need to maintain the operation of the phenomenon; 6, a large volume of water boiler design, the load fluctuation of furnace not sensitive to large changes in the load range of users still apply. 7, industrial boilers professional artists and designers carefully designed appearance, novel and unique and yet with the surrounding environment coordination. Sino-Swiss boiler completely changed the image of heavy industrial boilers, industrial boilers is a new concept of low-carbon twenty-first century. Construction and installation points: 1 explosion-proof door is provided on the fuel, the rear of the gas-fired boiler or pipe smoke, explosion door location should be conducive to explosion venting. For gas explosion likely to endanger the safety of the operator occasions, should be installed on the guide tube pressure relief blast doors. 2. Installation of boiler and its auxiliary equipment, water treatment equipment should meet the technical requirements of the device manufacturer. Equipment foundation must be the arrival of equipment and after verification and design drawings before construction. 3. When mounting the device, the device should be avoided, to install the floor material are collected together. Column using a construction, the beam lifting device, must first verify that the carrying capacity of the beam, the column. 4. After the pressure test acceptance oil, gas, water, steam pipe installation, according to "Industrial metallic pipeline construction and acceptance" in GB50235-1997. The main construction practices and node configuration detail see National Building Standard Design Atlas. 02R110 "Gas (oil) boiler room engineering design and construction Atlas" 02R111 "small vertical, horizontal tank Atlas" 02R112 "Tank dome Atlas"Free Chat
Copyright © 2020.Company name All rights reserved.