Boiler fire phenomenon, how to do 1, furnace pressure fluctuations or to limit and alarm. 2, no flame detector flame, flame flameless television display. 3, flue gas oxygen abnormal fluctuations. 4, steam pressure steam temperature dropped drastically. 5, furnace black, black smoke chimney. 6, the flue gas temperature is reduced. 7, MFT action, turbine trip, splitting the unit. Cause 1, the furnace combustion conditions organizations unreasonable, improper wind coal proportion. 2, the load is too low, unstable combustion conditions without oil combustion vote, or vote, although oil but not good combustion results. 3, cast oil, poor quality oil, oil spray gun is bad, low oil pressure, oil system failure. 4, poor coal quality, coal is too rough, the water is too large pulverized coal combustion adjustment is not timely. 5, the primary air temperature, air pressure is too low. 6, boiler MFT protection action. 7, a large area of the furnace coke collapse, smashing off the flame. 8, severe water wall pipe explosion will blow out the flame. 9, all coal-fired condition, mill pulverizing system failure caused most or all trips. 10, a part of auxiliary machinery such as a fan, blower, fan, air preheater tripped, causing unstable furnace combustion conditions. 11, sootblowing properly, resulting in a large number of normal operation of the furnace ash effects of fire inspection of the boiler. 12, bottom seal damage. Treatment 1, the boiler fire, MFT should be action, otherwise manual MFT. 2, normal inspection device linkage linkage MFT, confirm that all fuel cut. 3. quickly identify the cause, try to eliminate the boiler can be re-ignition, the recovery unit operation. 4, when the mill started again after the trip, the trip must be the primary air tube mill full purge. 5, the MFT operation, checks, Fan normal operation, automatic furnace vent. 6, the MFT movement, check all the secondary purge air damper position is set, the total air volume is automatically adjusted to 30 ~ 40% BMCR sufficiently purged air volume. 7, the MFT operation, when the turbine is in a state disk drive, the disk drive must continue until the normal turbine eccentricity, before re turn red. 8, if temporarily unable to identify or eliminate the cause, restart and could threaten personal safety equipment, non-start. 9, processing according to the corresponding predetermined remaining MFT.
Hot water boiler for users to solve the "coal" urgent at present, energy conservation and building sustainable economic model has become a national priority, but only our coal utilization hovering around 30%, far below the 78 % of the international average. Steam boiler is an energy conversion device, the energy input to the boiler fuel chemical energy, electrical energy, thermal energy and other forms of high temperature flue gas, and after converting the boiler, the steam output having a certain outside thermal energy, high-temperature hot water or an organic carrier. Biomass boiler categories: biomass boilers Horizontal, vertical biomass boilers. Biomass gas thermal oil heaters, biomass factory selling steam boiler, biomass hot water boiler, biomass oil furnace. Gas-fired steam boiler burner underlying mode, two-pass configuration, the fuel combustion, the boiler operation is stable and take up less space, while the spoiler is inserted smoke tube, smoke slow speed, increase heat transfer, a high thermal efficiency, reducing user fees Therefore, improving the utilization of coal combustion has become essential. Currently, coal-fired hot water boiler control system to achieve precise control and real-time monitoring. By controlling the water temperature, the fan speed to achieve a controlled, to ensure the stable combustion furnace pressure and coal, which saves coal, but also to ensure safety. Industrial production in the boiler and heating primary energy into secondary energy of important equipment, has been widely used in industrial production and daily life. Coal-fired hot water boiler control scheme is reasonable and convenient way to monitor, steady state operation, the whole process of thoughtful service, users get a good feedback. I believe in the future, coal-fired hot water boiler intelligent control scheme can serve a wider field of industrial production, as well as hotels, schools, hotels, residential heating, bath, hot water and other fields, coal cost savings for users, improve combustion efficiency, ensure the safe operation provide a solid guarantee. Completely solve the problem of long-term accumulation of the user, the water temperature stable. Water temperature set by the ambient temperature, grate speed difference adjustment according to the actual water temperature and the set temperature of the water, i.e. adjusting the amount of coal boiler, to ensure the stability of the water temperature. Outstanding energy saving. Grate speed changes to the feedforward signal, in conjunction with flue gas oxygen content signal or the furnace temperature, blower speed control using the PID algorithm, to ensure full combustion of the coal, to improve the utilization of coal, reduce emissions of harmful substances. Excellent safety performance. To change the fan speed as a feedforward signal, the PID control calculation and induced draft fan speed according to the furnace pressure value, to ensure the stability of the furnace pressure. This paper introduces a control algorithm based on the level of intelligence of the new big jump lag PID. After control of embodiment, given a certain waiting time to observe the effect, and to determine whether further embodiment control, multi-parameter input and multiple output control mode based on performance parameters.
Due to the special nature of the industrial park location, we are more to consider whether the boiler with green features in the choice of boiler equipment. According to our survey of the entire boiler industry, quick side has considerable experience in research and development in the field of environmental cleaning boilers, boiler equipment while also providing low pollutant emissions for Beijing more enterprises and institutions, we are fully confident that the fast boiler ability. --customer feedback
Small factory selling steam boiler Description: Small steam boiler refers to the amount of evaporation per unit time is small and low steam pressure steam boiler, steam boilers generally small volume refers to less than 30 micro-liters exemption steam boiler, the mechatronic device, host auxiliary integrated, easy to use, simple to install, simply connect the power, water and heat can, installation, use and technology supervision department supervision is not. Working principle: Its basic principle is: by an automatic control device, to ensure control liquid during operation or high, medium and low probe feedback control electrode opening of the pump, is closed, the amount of water the length of time the heating furnace; it is set by the pressure switch with the constant maximum output vapor pressure steam, the water level falling furnace, when in the low water level (mechanical), water level (electronic), automatic water pump, to the high level, the pump is stopped replenishment; At the same time, the electric tube furnace heating was continued, a steady stream to produce steam, the upper portion of the top panel or instantly display the steam pressure gauge pointer value, the whole process can be automatically displayed by the indicator. Product: Small steam boiler in accordance with the fuel can be divided into small electric steam boilers, small fuel steam boilers, steam boilers and other small gas; in accordance with the vertical structure can be divided into small steam boilers, horizontal steam boiler small, mostly single small steam boiler , double the return of the vertical structure, large steam boiler three-pass mostly horizontal structureFree Chat
Copyright © 2020.Company name All rights reserved.