To prevent air pollution and ecological damage, protect and improve the environment, promote the construction of ecological civilization, and promote sustainable economic and social development, Nanjing, Jiangsu Province to develop and launch the "Nanjing Atmospheric Pollution Prevention Act," played on May 1, 2019 official implementation.
1, the implementation of energy consumption and total coal consumption control and intensity control system. City of total energy consumption and coal consumption control administrative department with the relevant departments in accordance with provincial and municipal energy conservation requirements, the preparation of periodic control energy consumption and total coal consumption embodiment, the Municipal People's Government for approval.
2, high-pollution fuel combustion zone ban prohibits the sale, burning polluting fuels; prohibit new or expanded high-polluting fuel burning facilities; has been completed, should stop using within the prescribed period the Municipal People's Government, or switching to natural gas , liquefied petroleum gas, electricity and other clean energy.
4, petrochemical enterprises should strengthen the recovery of combustible gases. Flaring device should be used to deal with emergencies, not as a daily air pollution treatment facilities.
5, to encourage the production, use, or free of volatile organic compounds less volatile organic content of the feedstock and products. Surface coating, packaging, printing, furniture manufacturing and other industries should use low VOC content of products. Petrochemical and other organic solvent, the company should improve the production process, a low content of volatile organic materials and products.
6, resulting in production and business activities of volatile organic waste gas should be carried out in a confined space or equipment, and the installation of, use of pollution control facilities. Shipbuilding and other production and business activities can not be carried out in a confined space, and building (structure) building routine maintenance of live animals, roads, bridges, etc., should take effective measures to reduce emissions of volatile organic compounds.
Gas-fired steam boilers are a very wide range of special equipments, widely used in food, chemical, paper, textile, construction and other industries. In the process of loading and installing a gas steam boiler, some problems must be paid attention, otherwise it may cause a certain degree of economic loss.
1. Pay attention to the following matters during the loading and unloading and handling of gas-fired boilers: the lifting capacity of the lifting equipment should match the weight of the lifting boiler. The lifting lug on the boiler with the lifting lugs that cannot be used for lifting can not be used for lifting. The length of the steel cord should be reasonably selected to avoid the scratching of the furnace due to the improper length of the steel cord. The boiler must be protected from any damage during handling and handling.
2. Reserves for maintenance space When installing boilers, ensure that there is sufficient maintenance space around the boiler.
3. Setting and precautions for the base and base of the gas steam boiler The boiler body must be installed on the basis of 100-150mm above the floor of the boiler room. It must be confirmed with the technical personnel of the boiler manufacturing company in advance and constructed according to the basic drawings. The anchor bolts must be reserved on the foundation. The foundation shall be capable of withstanding the maximum weight of the boiler and the amount of water it holds. When installing the base, you must first position it. After positioning, adjust to the same length of the two diagonals of the base, and then tighten all the fixing bolts. The installation of the base is carried out with reference to the reference line.
4, general precautions Be careful not to tilt and impact the boiler and accessories too much. No combustibles can be placed around the boiler. Do not use oil and water to smother the boiler. The boiler should normally be installed in a separate boiler room. The new gas-fired boiler room should not be connected to the house. The boiler room shall not be connected to Class A, Class B and Category C fire hazard rooms using flammable liquids. If connected to other production plants, the application firewall is separated.
5. The fire resistance grade and fire protection requirements of the boiler house building shall comply with the requirements of the Code for Fire Protection of Building Design and the Code for Fire Protection Design of High-rise Civil Buildings. The ground of the gas steam boiler room should be flat, non-flammable, no water accumulation, and the foundation load should meet the requirements. The power supply voltage of the gas steam boiler room should be stable to avoid causing the electrical components to burn out. If the voltage is unstable, it is recommended to install a voltage regulator. Ventilation equipment should be installed in the boiler room, and the boiler should be kept at room temperature below 50 °.
Selection of how gas hot water boiler? Gas hot water boiler as the name suggests refers to the fuel gas hot water boiler, gas hot water boiler big advantage is energy saving and pollution-free, compact, small footprint, high degree of automation, automatic operation. Gas and oil-fired boiler and hot water boiler electric boiler is compared to the most economical, most people choose as a gas hot water boiler fuel steam boiler suppliers, heating and bathing equipment.
Coal-fired boilers to gas boilers benefits and precautions With the rapid development of national energy-saving environmental protection, the traditional coal-fired boiler can not meet the needs of the times. Therefore, the coal-fired boiler biomass boiler or gas boiler has become in many boiler user's choice. Before the transformation, to understand the difference between .1 and gas boiler fired boiler. Circulating fluidized bed combustion boiler fired by coal crushing device fluidized combustion process, the coal by crushing device percutaneously into the bunker through a the spreading coal coal injecting air into the furnace; circulating ash by heating, fluidized combustion process. When the coal into a gas fuel is injected directly into the combustor for combustion. 2. Combustion of Coal is mainly composed of C, H, O, N, S, ash and moisture and other elements. Generated when coal SO2, SO3, NOx ash and moisture, and SO2, SO3, NOx from flue gas emitted into the atmosphere, pollute the environment and cause harm to humans. The main components of the exhaust gas and coke are CO and H2. The main produce CO2 and H2 post-combustion, much lower than coal-fired boiler SO2, SO3 and NOX emissions. 3. Ventilation pressurized combustion coal combustion boiler used in a combustion mode. The bottom of the combustion process through the induced draft fan with fan and completed. In the combustion of coal, it requires a lot of air. Gas under a slight positive pressure in the boiler or burner slightly negative pressure, which requires less airflow. Burner air may be pre-mixed with natural gas. 4. coal boiler control reasons, material thickness, amount of wind, the wind volume, wind and other than coal, coal-fired boiler is difficult to automatically adjust the operating parameters of the boiler according to the load. However, fewer factors gas boiler, the burner valve can be adjusted according to the size of the load, easy to implement automatic control. Coal-fired boiler to a gas boiler Notes: Main results are as follows: (1) small boiler, the coal-fired boiler to a gas boiler, i.e. the negative pressure of combustion from the original to the current combustion slight positive pressure, and must pay attention to the furnace wall structure sealing problems. Closely related (2) selection and arrangement of the burner and furnace, the degree of filling of the flame in the furnace is preferably not formed dead air, to avoid the interference of adjacent flame burners, to avoid interference from adjacent burner flame. Unburned gas - air mixture should not be in contact with a heated surface, in order to avoid incomplete combustion. Gas combustion. Gas burner arrangement disposed conduit and ducts should be considered reasonable gas pipe and duct arrangement, ease of operation, inspection and maintenance. (3) the transformation of coal-fired boilers is mechanized layered gas boiler should be removed before the arch and the arch, and the bottom heating surface increases, in place of the grate, the grate to prevent overheating. Gas Velocity (4) on heat transfer surface of the fly ash is not restricted abrasion conditions, convection heating surface heat transfer coefficient is increased, increasing the pressure in the boiler where H is unduly increased. Boiler erosion surface. At this time, the capacity of the boiler should be noted that the steam separator to ensure the quality of the steam.Free Chat
Copyright © 2020.Company name All rights reserved.