Wuhan Yu Dahua Group Co., Ltd. is a cotton based, weaving, knitting and textile car decoration installation in one of the cross-industry, diversified and comprehensive export-oriented enterprise groups. 2017, the Group expanded production scale textile processing, the number of new production lines, the Group's original steam boiler for hotel company can not meet the growing demand of orders in urgent need of a new steam boiler purchase. When selecting vendors steam boiler, the boiler output device side fast sustainable high quality steam attracted, decided to cooperate with the fast boiler. Fast art by side to the user site needs analysis, to provide two integrally condensing gas steam boiler (WNS4-1.25-Y.Q).
Electric boiler for hotel company is an indispensable heating gas in winter, that is, the most important electric boiler is not suitable to place combustible materials (paper, cloth and other combustible materials) around the boiler, which can reduce the occurrence of fire from the source. 2. Electric heaters do not have plugs, plugs forget to be unplugged and resistive wires are overloaded, or aging plugs and cables can also cause fires. 3. When using electric heaters, people should always be kept on the edges, and power plugs should be unplugged when they are not in use. Many people do not have the habit of unplugging the switches, but this will also give a fire a chance of fuelling. 4. If there is a sudden power outage, Unplug the heater to prevent incoming calls A fire broke out with a sudden increase in electric current.
01. Thermal control system classification of fuel-fired gas-fired boiler (1) Electric instrument combination system mainly consists of relay, time relay, program relay and so on, which consists of program control and interlock protection system; The monitoring and regulating system is composed of electric unit combination instrument or digital and intelligent series instrument, measurement and display instrument, acousto-optic alarm instrument and so on. The design experience of electric instrument system is mature and the price is cheap, but it is difficult to realize the redundancy of the system, data transmission and maintenance, and it is also difficult to realize the advanced control method. The electric instrument system is mainly used in the small boiler, but the electric unit combination instrument is used in the closed loop adjustment. The use of cases has been reduced year by year, almost replaced by intelligent multi-functional instruments, The electrical unit assembly instruments mentioned in the following sections are simply intended to illustrate the principle and composition of the regulation system using a series of instruments familiar to the industry and widely used in that era. (2) the core of programmable control system is programmable controller (PLC). The programmable controller has been widely used in logic control at first, and the ability of process control has been increased since 1990s, which makes the application of programmable controller in the field of process control more and more extensive.
Gaz than steam boiler for hotel company should be how to calculate? Q: ratio of gas steam boiler gaz simple algorithm is multiplied by the calorific value of coal and boiler efficiency is calculated by dividing this simple assumption does not heat to the steam boiler efficiency of 80%, coal calorific value 5500, if the amount of steam produced a ton of coal can be calculated as follows * 0.8 = 5500/600 = 7.3, ie: gaz ratio of 7.3 can be calculated simply, is this right? A: According to your argument: the amount of steam a ton of coal produced, commonly referred to as the evaporation rate of the fuel, commonly known as steam coal ratio. The calculation formula is: base received low calorific value of coal is then divided by multiplying the thermal efficiency of the boiler (steam heat feedwater minus heat). You said above is correct.
With the increase of air supply volume, the mixture of oil mist and air is improved, which is beneficial to combustion. However, if the air volume is too large, the furnace temperature will be decreased and the incomplete combustion loss will be increased. At the same time, the heat loss of exhaust gas will be increased and the power consumption of the fan will be increased because of the increase of flue gas. If the air volume is insufficient, the combustion will be incomplete, resulting in carbon deposition at the tail, which is prone to secondary combustion accidents. Therefore, each boiler for hotel company should pass the thermal efficiency test to determine its economic air volume at different loads. In practice, the stoves usually take into account the ignition of the nozzle and the carbon dioxide or oxygen content in the flue gas. Content to adjust the supply air volume. If it is found that the combustion condition of a nozzle is not good, or if the atomization plate with different aperture is replaced, the air pressure of the supply duct should be kept unchanged, and the opening degree of the duct baffle of the nozzle should be adjusted to normal combustion. If the fuel quantity changes due to the change of the oil pressure in front of the furnace, the opening of the fan baffle should be adjusted to achieve normal combustion by changing the air pressure and air volume of the air supply duct when it is necessary to adjust the supply air volume.
3) the observation and analysis of all kinds of flame when adjusting the fuel oil. Generally through the fire point adjustment and flame center adjustment to complete the flame adjustment. The ignition point of the oil mist should be close to the nozzle, but there should be no tempering. Early ignition is beneficial to complete combustion and stability of oil mist. However, the fire is too early, too close to the nozzle, easy to burn the nozzle and furnace wall to determine the mouth. Furnace temperature flying oil varieties and atomization quality, as well as air volume, wind speed and oil temperature, will affect the distance and proximity of the ignition point. So if you want to adjust the ignition point, you should find out the cause in advance, and then take targeted measures. When the boiler load is constant and the oil pressure and oil temperature are stable, Should be based on the ignition point wind speed and wind distribution situation.Free Chat
Copyright © 2020.Company name All rights reserved.