Fangkuai Boiler is a clean-up vertical steam heating boiler equipment based on various excellent scientific and technological advancements, focusing on product development, manufacturing, and manufacturing that are more efficient, environmentally friendly, and energy saving, and meet the basic national conditions of environmental protection in China. In order to promote the rapid development of the heating furnace manufacturing industry, people-oriented, consider the specific requirements of customers in the manufacturing industry for heating furnaces in various industries.
Operation of the vertical steam heating boiler, including what? Including the operation of the boiler, what does? Following on from the Henan fast boiler company to tell you about: 1. The water level regulation of normal water level in the middle of the gauge (1) of the boiler. Operation with the magnitude of the load is adjusted: to maintain a high level during low load, high load to maintain a low level. Changes should not be down more than 40 mm. (2) to be run on the water level gauge to compare the two groups, if the water level display should be corrected promptly identify the cause. (3) To achieve a balanced continuous boiler feed water, ground water supply, water supply less, to maintain the water level in the normal water level fluctuates slightly in the vicinity. (4) load change is large, prone to false level. Pay attention to judgment, in order to avoid misuse. 2. Steam pressure regulator (1) when the boiler must constantly monitor the pressure gauge indicated. To maintain stable steam pressure, boiler pressure must not exceed the design pressure. (2) increasing the boiler load: Steam pressure decreased boiler load is increased, if the level is high at this time, the amount of water should be reduced to a water supply or suspend, the amount of coal and increase the air volume. Gradually increase the amount of water at the same time to strengthen the burning, keep the steam pressure and the water level is normal. (3) boiler load reduction: the vapor pressure rises to reduce boiler load, if the level is high at this time, the amount of coal should be reduced and the air volume, reduced combustion. Then the appropriate water reduction or suspension of water supply to the water vapor pressure and stability in the nominal range. Then press the normal combustion and to adjust the amount of water. If the actual water level within the boiler is low, to increase the amount of water should, until the water level returns to normal after the combustion and needs to be adjusted according to the water vapor pressure and load changes. 3. Combustion adjustment (1) combustion index. Normal combustion boiler comprises a uniform supply of the fuel, reasonable ventilation, adjusting three basic aspects combustion. B. maintain a high temperature of the combustion chamber temperature of the upper layer is preferably in the 1100-1300 ℃, flame orange in color. Flame reddish color indicates that the amount is not enough to the wind, the color white indicates that excessive wind. It should be appropriately adjusted. C. fuel ash to reduce ash content in the combustibles to be below 10%. d. reducing the temperature of the exhaust gas boiler exhaust gas temperature should be controlled below 200 ℃. e. excess air negative pressure holding furnace boiler 1.2-1.4, by adjusting the balance of the blowers to maintain the furnace pressure is 2-3mm. F. to improve the thermal efficiency of the boiler thermal efficiency of the boiler should be kept above 60%. (2) adjusting the combustion a. Reasonable amount and the distribution of fuel to the amount of air needed for combustion. Ventilation should first increase the amount of fuel increases, it should first reduce the amount of fuel supply reduced ventilation. b wind principle feature: burn promoting intermediate ends. That is, after the coal into the coal starts to warm up the shutter, fire line front arch, the primary combustion zone, the middle grate to burn the rear grate zone. c is the normal combustion conditions: fuel ignition start at 300mm from the shutter of coal, even flames, the fire bed formation, at the end away from the combustion grate at the end of 300-500mm. d. Hold appropriate furnace temperature to avoid coking. E. fire bed to maintain the homogeneous combustion, to avoid burning fire bed obliquely. F. less than 30 minutes residence time of the fuel on the grate. Our company provides services related to the installation of the boiler!
2 t 2 t introduce gas vertical steam heating boiler gas boiler burner arranged good technical performance, the use of automatic combustion ratio adjustment, automatically adjust the water supply, the program start and stop, automatic operation and other advanced technology, and having a low water level and low level alarm, high . steam pressure, turn off automatic protection function of the boiler has a compact, safe, reliable, simple, rapid installation, low pollution, low noise, high efficiency features: 2 tons of gas steam boiler with a leading domestic level, and industry compared to the same parameters of the boiler, with a compact, power, fast boosting, high thermal efficiency. Advantages: use all wet back shell type pyrotechnic tube structure. This structure because of its compact structure, small footprint, originally applied in the marine boiler. This architecture uses three return, the oil mixed with air or gas well through the atomizing burner, complete combustion in the furnace in a corrugated, folded from the rear chamber into the first tobacco smoke return pipe to the front smoke box to the second return pipe tobacco, cigarette box, is discharged after the last to enter the chimney.
The advantages of gas steam vertical steam heating boiler Gas steam boilers advantage: designers will arrange commandment information again, simple and convenient operation of the facility. Gas-fired steam boiler is not only easy to operate, and as soon as possible to ensure the safety factor used. Energy-saving advantages: high-temperature gas steam boiler with characteristic base pressure, greatly reducing the use of water pressure level heating facilities, to immediately benefit from lower capital injection facilities. Also said that the proportion of raw materials and gas touched. Only proper and adequate oil ignited gas can produce ratios exceeding ignite rate, together with its ability to reduce vapor emissions and maintain two-way power-saving, very convenient. Gas steam boiler can be arranged according to the specific needs of the amount of vapor, reduce renewable resource conservation. The higher the specific requirements and the intermediate supply pairing methodology, the higher the power saving effect. The heat exchanger can continue to use sewage water calories, and thus can increase oxygen supply and drainage of water temperature. In accordance with the provisions of the Environmental Protection useless now need, doing everything, gas-fired industrial equipment is more commonly used. In severe conditions, serious vapor watering, the water content of the salt to enhance the micro gas steam boiler, water hammer audible in steam lines, steam splashing outwardly coupling joint living; or furnace tube if economizer line split, water vapor allowance is given below, when less water is generated, in turn, the situation will occur; less water when severe, it is possible to see the red water wall of furnace tubes can also smell burnt taste. Together, furnace tube will split, could hear explosions. Steam and smoke exclude the furnace mouth and fire security door from. Low water interlock device, if the amount of water is less than the target value, air-conditioning fan, booster fan and grate machine motor reducer operation should be terminated; Security Council water is less than the low water mark, water glass (plate) is black; cleaning sheet is not water clear micro gas steam boiler is not filled or slightly severe filled with water? Ways: first turn off the water level gauge, tap water pipe is connected, and then open the drain cock. If you can see the water line from the top lower, then it is filled with a little water, open the drain valve and place no problem of water. If severe filled with water, please use the emergency shutdown countermeasures.Free Chat
Copyright © 2020.Company name All rights reserved.