Gas-fired fired steam boilers and pressure hot water boiler has what a difference, the most critical is that goods difference: pressure hot water boiler production part of the standard high-temperature water; the production of gas steam boiler is part of the standard steam. Second, the auxiliary little difference: like supporting pressure hot water boiler water circulating pump, does not need gas steam boiler; gas steam boiler water level gauge support, do not need pressure hot water boiler; gas cylinder steam boiler supporting points, pressure hot water boiler with tank; Third, the production boilers, boiler installation, a boiler, a steam boiler safety of the gas stringent requirements. Fourth, the key difference is the use of gas boilers steam production is saturated standard high pressure gas for power generation, tie-dye, medical and other fields, is due to the production of saturated steam, pressure equipment is therefore, a boiler and the boiler installation must meet Compliant pressure hot water boiler is the production of high temperature water, not a pressure equipment. How to gas steam boiler blowdown gas boilers | oil boiler | Environmental Equipment Co. steam boiler (1) open inside discharge water valve; (2) slow external open blowdown valve, and the discharge duct for warming; (3) back and forth on the exterior from the opening and closing of the blowdown valve, the buffer boiler dirt stains, so that the dirt is discharged as water stains; (4) the inner blowdown valve closed, the waste water stored between the two valves drained water; (5) external blowdown valve closed, to complete the discharge.
Gas boiler Burner Failures and gas boiler burners Failures and - best ￼ a gas boiler, gas boiler burner ignition misfire rod reasons: 1, the ignition bar gap interposed carbon residue with oil. 2, ignition rods fragmentation. moist. Leakage. 3, the distance between the ignition does not stick, too long or short. 4, ignition rods Insulation damage, short to ground. 5, ignition cable and transformer failure: cable, connector damage caused by a short circuit during ignition; transformer break or other fault occurs. Measures following five: Clear, renewal, adjust the distance, change and switching transformer. Second, gas boiler, but spark ignition rods misfire reasons: 1, the cyclone disc space ventilation is blocked carbon, poor ventilation. 2, dirty oil nozzle clogging or wear. 3, the throttle angle is set too small. 4, the firing bar from the leading edge from the oil nozzle tip inappropriate (too protruding or retracted) 5, the first solenoid valve is an oil debris blocking gun (gun small kerosene). 6, oily or too viscous to flow easily clogged or the oil filtration system the valve is not opened, so that insufficient suction pump, oil pressure. 7, the filter pump itself blocked. 8, the oil more water (boiling abnormal noise within the heater). Measures are: Clear; first wash, such as not renewed; turndown test; adjusting the distance (in 3 ~ 4mm as well); Remove cleaning (cleaning the parts diesel); Check tubing and oil filters, insulation equipment ; remove peripheral screw pump, carefully remove the cover inside out oil network, with immersion oil; renewal of the test oil. Third, when the gas boiler and turn the fire a small fire normal, off, or flashing instability reasons: 1, the air volume damper setting fire too. 2, oil fires micro switch valve (damper outermost that group) inappropriate setting (set throttle air flow rate is greater than the fire). 3, oleaginous easy to spray viscosity is too high (heavy). 4, and the nozzle plate spacing cyclone inappropriate. 5, fire nozzle worn or dirty. 6, the preliminary fuel tank temperature is too high, so that the steam not smooth oil pump oil feed. 7, fuel oil boiler water. Action: Test gradually reduced; heating temperature; adjusting the distance (between 0 ~ 10mm); clean or replace; approximately set to about 50 deg.] C; or drain oil change. Fourth, the noise increases gas boiler burner reasons: 1, cut-off valve is closed or the passage into the fuel shortage, an oil filter blockage. 2, the oil inlet temperature is low, the oil viscosity is too high or the temperature is too high the pump inlet. 3, oil pump failure. 4, fan motor bearing damage. 5, dirty fan impeller. Processing methods: ① the oil line check valve is open, if the oil filter is working properly, the filter cleaning pump itself. ② heating oil or reduce the oil temperature. ③ Replace the oil pump. ④ replace motor or bearings. ⑤ cleaning fan wheel.
The only example of an ultra-low nitrogen oxide emissions through boilers Enterprise Test - fast boiler, the production of gas hot water boiler, gas fired steam boiler, condensing boiler integrated, NOx emissions is far below the required standards, environmental protection departments successfully passed the test and get the user's praise.
Natural gas boiler is a kind of thermal energy conversion equipment, which uses natural gas, liquefied gas, city gas and other gas fuels as fuel to burn the heat released from the furnace, heat the water in the pot, and make it vaporize into steam. Water in a pot (drum) is constantly heated by the burning of gas fuel in the furnace to heat up the temperature and produce pressurized steam. Because the boiling point of water increases with the increase of pressure, the pot is sealed, and the expansion of steam in the boiler is restricted to produce pressure to form a thermal force. Strictly speaking, the steam of a boiler is heated to saturated water and vaporized in the drum at constant pressure. It is widely used as an energy source. Natural gas boiler heating In order to protect indoor warmth and human health, so when choosing natural gas boilers, safety issues are very important, and quality issues can not be ignored, only with good quality, in the use of more assured. Some services can also be done better, the choice of heating is customer satisfaction. Understanding natural gas boilers is certainly a need to know the sales situation of the products, if the natural gas boiler reputation is good, it is still very good in comprehensive aspects, worthy of consumer choice, the conversion of performance and thermal energy can also be consulted. There will be no problems when used like this, and there will be no need to worry about electricity during installation The pressure is not enough. Natural gas boiler shut-down method: after stopping the powder feeder, blow the primary duct for 5 minutes before stopping the oil gun. Oil guns should be blown one at a time, not multiple at the same time. After blowing the gun, ventilate the furnace of natural gas boiler for 5 minutes for 8 minutes, and the air volume is not less than 20% of the rated load. To remove combustible material from the furnace. According to the fuel, natural gas boiler can be divided into natural gas fired steam boiler, city gas steam boiler, coke oven gas steam boiler, liquefied petroleum gas steam boiler, etc. According to the structure form, it can be divided into vertical steam boiler and horizontal steam boiler. Natural gas boiler is shell type Full wet backflow three-way pyrotechnic tube structure, flame combustion in large combustion chamber micro positive pressure combustion, complete extension, low combustion heat load, high combustion heat efficiency, effectively reduce the exhaust temperature, energy saving and consumption reduction, use more economical, The heat absorption strength of the boiler is improved by adopting the structure of corrugated furnace tank and threaded smoke pipe, and the heat exchange surface is expanded to meet the need of heat expansion. It is scientific, reasonable and durable.Free Chat
Copyright © 2020.Company name All rights reserved.