Gas-fired steam boilers are a very wide range of special equipments, widely used in food, chemical, paper, textile, construction and other industries. In the process of loading and installing a gas steam boiler, some problems must be paid attention, otherwise it may cause a certain degree of economic loss.
1. Pay attention to the following matters during the loading and unloading and handling of gas-fired boilers: the lifting capacity of the lifting equipment should match the weight of the lifting boiler. The lifting lug on the boiler with the lifting lugs that cannot be used for lifting can not be used for lifting. The length of the steel cord should be reasonably selected to avoid the scratching of the furnace due to the improper length of the steel cord. The boiler must be protected from any damage during handling and handling.
2. Reserves for maintenance space When installing boilers, ensure that there is sufficient maintenance space around the boiler.
3. Setting and precautions for the base and base of the gas steam boiler The boiler body must be installed on the basis of 100-150mm above the floor of the boiler room. It must be confirmed with the technical personnel of the boiler manufacturing company in advance and constructed according to the basic drawings. The anchor bolts must be reserved on the foundation. The foundation shall be capable of withstanding the maximum weight of the boiler and the amount of water it holds. When installing the base, you must first position it. After positioning, adjust to the same length of the two diagonals of the base, and then tighten all the fixing bolts. The installation of the base is carried out with reference to the reference line.
4, general precautions Be careful not to tilt and impact the boiler and accessories too much. No combustibles can be placed around the boiler. Do not use oil and water to smother the boiler. The boiler should normally be installed in a separate boiler room. The new gas-fired boiler room should not be connected to the house. The boiler room shall not be connected to Class A, Class B and Category C fire hazard rooms using flammable liquids. If connected to other production plants, the application firewall is separated.
5. The fire resistance grade and fire protection requirements of the boiler house building shall comply with the requirements of the Code for Fire Protection of Building Design and the Code for Fire Protection Design of High-rise Civil Buildings. The ground of the gas steam boiler room should be flat, non-flammable, no water accumulation, and the foundation load should meet the requirements. The power supply voltage of the gas steam boiler room should be stable to avoid causing the electrical components to burn out. If the voltage is unstable, it is recommended to install a voltage regulator. Ventilation equipment should be installed in the boiler room, and the boiler should be kept at room temperature below 50 °.
Steam boiler fuel gas composition changes so the General Assembly cause flameout: fuel gas light oil fired steam boilers pressure off the fire caused by a sudden rise, the solenoid valve malfunction the gas supply interruption, the gas composition has changed so much moisture content is too high and so on. Blower, fan failure, the load is too low furnace pressure is too large excessive leakage and other excessive wind, so that the furnace temperature is too low can also cause steam boiler fuel flame. Causes fuel steam boiler flameout are: oil pump failure, the oil surface is exposed inhalation tube, clogging of the oil filter or oil supply pipe, a solenoid valve malfunction or misoperation caused by oil running intermittently. During transport the fuel with steam by heating water; inappropriate position inhalation tube with the pumping of water; improper contaminated oil floating on the water; poor dewatering tank drain plug such that the fuel with water.
Henan oil-fired boiler Introduction Product Introduction: Henan oil-fired boiler to run than electric heating boiler economic, easy to use than gas-fired boiler. With economic development and social progress and the improvement of people's awareness of environmental protection, coal-fired boilers due to serious pollution, moving away from sight, replaced by a new environmentally friendly digital boiler, such as electric heating boiler, oil boiler, gas boiler, electric heating boiler is more expensive, gas-fired boilers need to open a gas pipeline, then, if there is no gas pipeline, and hope boiler low operating costs, only select oil-fired boiler. Boot check: 1, various instruments, whether the instrument to confirm the adequacy of fuel tank, and the inlet valve is opened. 2, confirm the soft capacity and the water tank boiler water quality meets the requirements of the main valve is opened and boiler feed water inlet valve. 3, rotation of the oil filter to remove debris. 4, drain the remaining water in the boiler, while the opening operation of the low level alarm and chain. Features: 1, inserted within a fire retardant spoiler tube, slow speed exhaust enhance heat transfer, the temperature of the flue gas discharged from a low smoke chamber, reducing heat loss and save fuel. 2, furnace by computer-aided design, each of the heating surface is optimized, compact and reasonable arrangement, small boiler area, high thermal efficiency. 3, the user can set the start, shutdown time, after setting, no special duty, easy, and effort. 4, according to the boiler pressure furnace design, furnace provided with a top opening to atmosphere, the boiler is in an unpressurised state, there is no risk of explosion. 5, the inner fire tube inserted spoiler retardant, smoke slow speed, to strengthen the heat exchanger, combustion heat is conducted to a large extent in water, the discharged flue gas temperature is low smoke chamber, reducing heat loss and save fuel. 6, the water level sensor water level real-time monitoring, to continuously monitor the water level is normal furnace. While controlling the temperature and replenishment level sensor solenoid valves, the boiler water may be continuously supplied. 7, water boiler fuel water speed, water volume, widely used in factories, hospitals, schools, etc. required a large amount of boiling water units. Shutdown procedure: 1, when it is desired to deactivate the combustion boiler to the switch in the OFF position, the oil supply is stopped, the flame is extinguished, but the fan is still operating to blow away the residual flue gas in the furnace. 2, when the blower is stopped, the operation OFF switch to turn off the power and then, after closing the steam valve, and the fuel supply valve to close the valve. 3, open the drain valve when the discharge pressure is reduced after the boiler play an open valve, to drain the water in the boiler, and the steam partial open the drain valve to drain the water in the drum segregation. Daily checks: 1, check the water level regulator function: whether the automatic water pump stops. 2. Check flame monitoring. 3, is rotated, the slide cam portion lubricating, and wiping. 4, the flushing water level gauge 1-2 times (class), according to the proper operation, so that until the rinse water level gauge. 5, sewerage 1-2 times (class).
Major scientific and technological innovation is the State of the weighing, State of the weapon must be firmly in their hands, we must rely on self-reliance and independent innovation. - Xi Jinping December 14, kicked off at the Third International Fair of Innovation and Entrepreneurship Center at the National Convention. As China's first international "double hit" Expo theme show to the world maker culture: power generation, focusing on innovation! Fast Boiler Co., Ltd., Henan Province, to participate as an outstanding representative of the exhibition, at the provincial delegation of the booth, the party fast low nitrogen product model boiler and remote monitoring system is placed at the front, leaders at all levels attach great importance to the domestic foreign passengers .Free Chat
Copyright © 2020.Company name All rights reserved.