Boiler fire phenomenon, how to do 1, furnace pressure fluctuations or to limit and alarm. 2, no flame detector flame, flame flameless television display. 3, flue gas oxygen abnormal fluctuations. 4, steam pressure steam temperature dropped drastically. 5, furnace black, black smoke chimney. 6, the flue gas temperature is reduced. 7, MFT action, turbine trip, splitting the unit. Cause 1, the furnace combustion conditions organizations unreasonable, improper wind coal proportion. 2, the load is too low, unstable combustion conditions without oil combustion vote, or vote, although oil but not good combustion results. 3, cast oil, poor quality oil, oil spray gun is bad, low oil pressure, oil system failure. 4, poor coal quality, coal is too rough, the water is too large pulverized coal combustion adjustment is not timely. 5, the primary air temperature, air pressure is too low. 6, boiler MFT protection action. 7, a large area of the furnace coke collapse, smashing off the flame. 8, severe water wall pipe explosion will blow out the flame. 9, all coal-fired condition, mill pulverizing system failure caused most or all trips. 10, a part of auxiliary machinery such as a fan, blower, fan, air preheater tripped, causing unstable furnace combustion conditions. 11, sootblowing properly, resulting in a large number of normal operation of the furnace ash effects of fire inspection of the boiler. 12, bottom seal damage. Treatment 1, the boiler fire, MFT should be action, otherwise manual MFT. 2, normal inspection device linkage linkage MFT, confirm that all fuel cut. 3. quickly identify the cause, try to eliminate the boiler can be re-ignition, the recovery unit operation. 4, when the mill started again after the trip, the trip must be the primary air tube mill full purge. 5, the MFT operation, checks, Fan normal operation, automatic furnace vent. 6, the MFT movement, check all the secondary purge air damper position is set, the total air volume is automatically adjusted to 30 ~ 40% BMCR sufficiently purged air volume. 7, the MFT operation, when the turbine is in a state disk drive, the disk drive must continue until the normal turbine eccentricity, before re turn red. 8, if temporarily unable to identify or eliminate the cause, restart and could threaten personal safety equipment, non-start. 9, processing according to the corresponding predetermined remaining MFT.
Gas-fired horizontal type steam boiler and gas steam boiler at any time there is any good compared to the country more and more attention to environmental protection, gas steam boiler has been a great blow, and relatively gas steam boiler by many users of all ages, in recent years, the country also strongly promote the use of gas-fired boiler, gas steam boiler then compared with the gas steam boiler what good is it? And today we work together to explore. Gas-fired steam boiler steam boiler and gas each accounted for half of the market, showing potential rival, but in the long run, gas steam boiler will obviously be the only dominant market. Do not believe, look! 1. Purchase costs: gas boiler is evident in the technical and auxiliary facilities are far ahead of the gas boiler, and it is equipped with a special gas burner. 1 steam boiler tonnage, for example, the price of gas than the gas boiler boiler on high about 30%. 2. Construction costs: The costs mainly from the boiler room. Because the corresponding auxiliary equipment more gas steam boiler, the boiler room in the building have a little more money. The gas boiler auxiliary facilities require little or automatic control and operation, and automatic alarm and automatic protection, not only save building costs, but also safe and reliable; Also connected to the gas pipeline, the burner will automatically supply gas can effectively save costs staff. The gas-fired boilers because of the need of coal on the program, so it needs some staff payroll. 3. Fuel cost: around this by looking at the actual specific fuel price can be clearly seen. The fact is that the amount of gas than the gas burned per hour for much more. 4. environmental costs: in the need to protect the environment, review the current gas boiler more strict. The gas steam boiler due to the operation of the economy, environmental protection and energy saving, as well as government policy to encourage more and more widely used.
Boiler + Things, security, intelligence is our reputation. Based on advanced networking technology, remote monitoring group launched the operating system of the boiler, which in the domestic boiler industry are unprecedented breakthrough, the country has more than 4,600 boilers supporting the remote monitoring system, safe and stable running.
The use of electric horizontal type steam boilers What are the requirements? General Electric steam boiler is to be converted into an energy form of heat, through the conversion of the boiler can be turned into heat energy of steam or hot water, which requires the use of gas when you have it steam boiler, steam boiler in the first before water is necessary to check each valve, steam pipe, pressure variations, water tables, etc. also note the drain valve is not also intact. after the steam inside the boiler should be kept clean to be used, to which water is after softening the outer glass tube in the water table to be equipped with rugged protective cover, but also to keep it clean after each use it is necessary to scrub, as well as to see the water level of the water table there rise or fall, if it stops phenomenon, we must immediately investigate the cause. after the adjustment is not just above the steam boiler safety valve.Free Chat
Copyright © 2020.Company name All rights reserved.