Tai Chi, Jiaozuo City, Jiaozuo City Sports Center is one of important sports infrastructure, a total area of 11.73 hectares, held several international events. With strict management in Henan Province for air emissions of pollutants, Jiaozuo City, also launched the governance of coal-fired horizontal water tube boilers, thermal power and other equipment. Jiaozuo Sports Center actively cooperate with municipal workers, took the lead from coal to gas activities, the serious pollution of the original extent of coal-fired boilers to replace gas boilers. Gas boiler cleaning binding understanding of the market, to achieve cooperation with the finalization fast boiler by providing a fast side 2.8MW integrally condensing gas hot water boiler (WNS2.8-1.0 / 95/70-YQ), it is used to Sports Center provides heating and hot water.
Gas horizontal water tube boiler Burner Failures and gas boiler burners Failures and - best ￼ a gas boiler, gas boiler burner ignition misfire rod reasons: 1, the ignition bar gap interposed carbon residue with oil. 2, ignition rods fragmentation. moist. Leakage. 3, the distance between the ignition does not stick, too long or short. 4, ignition rods Insulation damage, short to ground. 5, ignition cable and transformer failure: cable, connector damage caused by a short circuit during ignition; transformer break or other fault occurs. Measures following five: Clear, renewal, adjust the distance, change and switching transformer. Second, gas boiler, but spark ignition rods misfire reasons: 1, the cyclone disc space ventilation is blocked carbon, poor ventilation. 2, dirty oil nozzle clogging or wear. 3, the throttle angle is set too small. 4, the firing bar from the leading edge from the oil nozzle tip inappropriate (too protruding or retracted) 5, the first solenoid valve is an oil debris blocking gun (gun small kerosene). 6, oily or too viscous to flow easily clogged or the oil filtration system the valve is not opened, so that insufficient suction pump, oil pressure. 7, the filter pump itself blocked. 8, the oil more water (boiling abnormal noise within the heater). Measures are: Clear; first wash, such as not renewed; turndown test; adjusting the distance (in 3 ~ 4mm as well); Remove cleaning (cleaning the parts diesel); Check tubing and oil filters, insulation equipment ; remove peripheral screw pump, carefully remove the cover inside out oil network, with immersion oil; renewal of the test oil. Third, when the gas boiler and turn the fire a small fire normal, off, or flashing instability reasons: 1, the air volume damper setting fire too. 2, oil fires micro switch valve (damper outermost that group) inappropriate setting (set throttle air flow rate is greater than the fire). 3, oleaginous easy to spray viscosity is too high (heavy). 4, and the nozzle plate spacing cyclone inappropriate. 5, fire nozzle worn or dirty. 6, the preliminary fuel tank temperature is too high, so that the steam not smooth oil pump oil feed. 7, fuel oil boiler water. Action: Test gradually reduced; heating temperature; adjusting the distance (between 0 ~ 10mm); clean or replace; approximately set to about 50 deg.] C; or drain oil change. Fourth, the noise increases gas boiler burner reasons: 1, cut-off valve is closed or the passage into the fuel shortage, an oil filter blockage. 2, the oil inlet temperature is low, the oil viscosity is too high or the temperature is too high the pump inlet. 3, oil pump failure. 4, fan motor bearing damage. 5, dirty fan impeller. Processing methods: ① the oil line check valve is open, if the oil filter is working properly, the filter cleaning pump itself. ② heating oil or reduce the oil temperature. ③ Replace the oil pump. ④ replace motor or bearings. ⑤ cleaning fan wheel.
Daily maintenance of gas-fired horizontal water tube boilerDuring operation, the gas-fired boiler should pay attention to the following points: (1) the gas-fired boiler does not allow positive pressure combustion or smoke injection in the furnace because it is easy to burn out the coal hole cover. (2) the bottom floor plane of the gas-fired boiler shall not be watered up in order to prevent damp corrosion. The gas-fired boiler shall be inspected every 2 weeks and every 3 months after the operation of the gas-fired boiler. (1) the gas-fired boiler shall be inspected and repaired in an all-round way after the operation of the gas-fired boiler every 3 months. (1) the gas-fired boiler shall be inspected inside and outside the boiler. If the pressed part of the weld, steel plate inside and outside corrosion phenomenon, if found in serious defects should be repaired in time, if the defects are not serious, the next time the furnace shut down repair, if found When suspicious, but does not affect the safety of production, records shall be made for future reference. (2) after inspection, boiler primer may be applied on the surface to prevent corrosion. 4. Gas-fired boilers and boiler base shall be painted at least once a year. 5, There are dry and wet methods for the maintenance of gas-fired boilers: dry method and wet method. Dry maintenance method should be adopted when the boiler is shut down for more than one month. (1) dry maintenance method: after boiler shut-down, the boiler can remove the water from the furnace, and the method of dry maintenance shall be adopted under one month. (1) dry maintenance method: after the boiler has shut down the furnace, Thoroughly remove the internal dirt, rinse clean, dry the furnace with a slight fire (be careful not to fire), and then apply a 10-30 mm diameter lump of quicklime. The plates are arranged and placed in the pan, without contact with the metal. The weight of quicklime is calculated at the volume of 8 kilograms per cubic metre of the drum, and then all manholes, hand-holes, pipe valves are closed and checked every three months. If the quicklime is broken, it needs to be replaced immediately. When the boiler is re-running, the quick lime and the tray shall be removed. (2) Wet maintenance method: after the boiler has stopped the furnace, the boiler shall discharge the furnace water, thoroughly remove the internal dirt, rinse it clean, and reinject the treated water until it is fully filled. Heat the furnace water to 100 ℃, let the gas from the water out of the furnace, and then close all the valves, where the climate is cold, do not adopt moisturizing method, so as to avoid the furnace water Icing damaged the boiler.
9 major technical characteristics of the gas hot water horizontal water tube boiler you know? 1, according to atmospheric boiler design, boiler in a non-pressure state, there is no safety hazard. 2, the use of advanced multi-layer insulation centrifugal glass wool, steel for packaging famous white color, heat loss, anti-rust appearance 3, burner configuration imported brands, high degree of automation, automatic purge controller according to the instruction, the electronic auto-ignition, automatic combustion (gas) automatically adjusting the ratio of wind oil, security and stability performance, good combustion. And there are flameout protection device, ensure safe operation. 4, the computer controller hot water boiler, all the functions are stored on a magic smart chip, a key to power boilers, automatic timing, temperature operation, the user can set the start, shutdown time, after setting, without special duty, save time, and effort. 5, the inner fire tube inserted spoiler retardant, smoke slow speed, to strengthen the heat exchanger, the temperature of the flue gas discharged from a low smoke chamber, reducing heat loss and save fuel. 6, large font display temperature, easy to grasp and boiler operating conditions of the system, the water temperature can be freely set from 10 ℃ to 90 ℃, automatic boiler or heating system to provide users with life, bath with hot water. 7, the control system in accordance with the temperature control of boiler water circulation pump start and stop, boiler water circulating pump starts when the water reaches an upper limit temperature, lower than the hot water circulation pump stops when the water temperature lower limit. 8, horizontal fuel gas hot water boiler three return all wet back structure, using a large furnace, rough smoke tube design, increased furnace radiation heat absorption, the effective energy saving. Using threaded pipe and waveform furnace, greatly enhanced heat transfer effect, greatly saving fuel consumption. 9, while the machine is equipped with thermal protection (ultrahigh temperature furnace, the burner is automatically stopped and an alarm buzzer, the second over protection (the boiler shell temperature exceeds 105 deg.] C, the secondary circuit is automatically cut off), the lack of anti-dry protection of water (when water is lower than the low water level of the furnace, the boiler is stopped and an alarm beep), a boiler leakage protection (the control system detects electrical leakage, short circuit, automatically cut off the power).Free Chat
Copyright © 2020.Company name All rights reserved.