Startup boiler steam temperature does not mention how high do? A: In the unit to start the process, often encounter steam pressure has reached the requirements, and the steam temperature was too much difference, especially in front of the turbine and the blast furnace or red switch occurs. Should take the following measures: appropriate to increase the amount of coal to improve the furnace heat load; adjust the secondary air ratio, increase the amount of lower secondary air; improve wind, air pressure, increased gas velocity; hydrophobic and full of air and exhaust mother pipe in front of the main steam isolation all hydrophobic.
A heated boiler is called a boiler. Heat transfer oil, also known as organic heat carrier or heat medium oil, has been used as intermediate heat transfer medium in industrial heat transfer for more than 50 years. Based on the idea of forced cycle design, a once-through boiler is developed. Generally, coal, oil and steam are used as fuel, heat conduction oil is used as the medium, hot oil circulation pump is used to force the medium into liquid phase circulation, heat energy is transmitted to the heating equipment and then returned to the heating furnace for re-heating. High operating temperature at low pressure, and high precision control for medium operation. The heat utilization rate of the system is high, and the transportation and maintenance are convenient. The closed circulation heat supply is connected with the atmosphere, can extend the service life of the boiler, liquid phase or gas phase transportation heating. The boiler adopts three-way coil design, the system sets the expansion water tank, and realizes low-pressure and high-temperature heating. The coil structure is adopted, the heating surface is sufficient, and the expansion is fully absorbed. Imported low-NOX combustion machine, combustion charge, belongs to environmental protection products. Boiler can choose advanced touch screen computer controller and digital computer controller automatic control system. With automatic temperature regulation, automatic ignition, and differential pressure, overtemperature, quenching protection. Boiler manufacturing standards, strictly in accordance with the relevant national standards. Pot The use of furnace water quality requirements: some users believe that as long as the boiler to maintain water can be, the water quality is not a choice. In fact, the quality of water on the boiler or have an impact, the editor recommends that you choose clean tap water. Because if there are impurities in the water, the use of this impurity water will have some impact on the equipment. The impurities form a thick layer of scale on the inner wall of the boiler. Scale will gradually thicken with time, and the accumulation of thickness will affect its heat transfer efficiency, resulting in a waste of energy consumption. If the scale appears, it should be cleaned up in time, so that the heat can be concentrated in the scale, which is not easy to emit. .
Details installed gas boiler combustion system that we need to pay attention when installing a gas boiler combustion system, inviting professional staff in advance of the circuit diagram design, so that when installing the status line installation will not appear unreasonable. Also, pay attention to install some fire-fighting equipment, which can provide protection for our security. Unit ventilation should generally remain the total combustion air amount at the rated load. Combustion process controller provides a separate set of contact start-stop control. May be formulated in a variety of burner start-stop loop cascade control relay 10A is a fuse, relay start-stop control stops the control terminal may be connected to the burner, may directly control the power of the burner. Both constant pressure sensor, water power, fuel, gas pressure set value is detected after the automatic controller opens. Time pressure sensor, water supply, oil, gas, and their detection circuit, alarm and found the problem immediately shutdown flame protection, the controller automatically displays the point of failure, an alarm sounds machine. Installation room oil, gas line gas boiler, boiler room should be strictly in accordance with design, specification, and should refer to the burner. Fuel system pressure test after installation is complete, should be 1.25 times the working pressure (minimum test pressure of not less than 0.4MPa). After the fuel pipe installation system should be flushed with water or steam flushing, flushing should have approved technical measures, the number of washing is not less than the secondary blowing, blow up until the clean medium, should be cleared after the purge debris and dead. After installation of fuel system should be oil circulation system-wide test. The gas should be the shortest route to the burner, the air supply pipe diameter must be larger than the constant value parts of the burner duct.
As a leader in the fast side condensing gas boiler, in recent years, provide a clean boiler to Beijing multiple office units, was well received. I units through the preliminary investigation and contrast, select fast boiler, it turns out, party fast product does have quite a good cleaning environmental performance, in line with the Beijing municipal government requirements for air pollution emissions, the use of very at ease. --customer feedbackFree Chat
Copyright © 2020.Company name All rights reserved.