Coal-fired kenya breweries fired boilers economizer economizer effect to save the name suggests is a secondary member of coal fired boilers and the like for the device, the principle is to use the coal-fired boiler economizer flue gas heat exchanger for heating the feedwater. Economizer heat absorbing smoke, reduced exhaust gas temperature, by improving the thermal efficiency of coal-fired boilers, to achieve the purpose of saving coal. Secondly, in the coal-fired boiler feedwater into the drum, since the exhaust gas after the preheating heater temperature increased, reducing the temperature difference between upper and lower walls of the drum, the drum reduces the thermal stress of the upper and lower walls coal-fired boilers, to reduce the vertical drum wall temperature difference due to damage, protect the safe operation of coal-fired boilers, coal-fired boilers to extend the life of the road.
Since I began preparations for the 2018 ASME certification program, and at the beginning of the project preparation work since January this year, the project has entered a crucial stage of the implementation. Ms. Jiang Lianju quality system under warranty division led to ASME certification were careful overall planning work to develop a detailed plan of the evidence, and careful organization departments to participate in the work of the various stages of implementation.
Some of the causes direct impact on the thermal efficiency of horizontal steam kenya breweries fired boilers of the country are carrying out a blaze of glory roaring coal to natural gas operations, the choice of horizontal steam boiler, greatly reducing the fine dust contaminated with dust, along with toxic gases such as nitrogen oxides emissions It has also been suppressed. Thermal efficiency is a key measure of horizontal steam boiler, a good start and that is that let you look at some of the causes direct impact on the thermal efficiency of horizontal steam boiler. Through research departments, the heat loss of horizontal steam boiler is very important from two aspects: the combustion air-fuel ratio is not satisfactory and Smoke and heat loss. Smoke and heat loss reduction should be modified in the tail horizontal steam boiler soot waste heat recycling install, or choose would be more leading series condensing boilers. Combustion air-fuel ratio over the substandard Analysis: common horizontal ejector-type steam boiler burner choice, without the formation of air-fuel ratio can be flexibly adjusted. Most of the horizontal steam boiler selected non-automatic strong emission burner, leading to the root causes of unsatisfactory air-fuel ratio has the following areas: air-fuel ratio is not ideal is more important is divided into two kinds of probability: When an excess of oxygen, there will be endless excessive cold air is heat conduction, resulting in increased energy consumption horizontal steam boilers, hot horizontal steam boiler efficiency decreased; when oxygen is not standard, incomplete combustion occurs, generating heat horizontal steam boiler efficiency decreased.
6 tons adjusting a combustion gas steam kenya breweries fired boilers, normal combustion boiler three basic aspects of indicators include a uniform supply of the fuel, reasonable ventilation, adjustment the combustion. 1, to maintain the high temperature of the combustion chamber temperature of the upper layer is preferably in the 1100 ~ 1300 ℃, flame orange in color. Flame reddish color indicates that the amount is not enough to the wind, the color white indicates that excessive wind. It should be appropriately adjusted. 2, fuel ash to reduce ash content in the combustibles to be below 10%. 3, reducing the temperature of the boiler flue gas exhaust gas temperature should be controlled below 200 ℃. 4, holding furnace negative excess air boiler is 1.2 to 1.4, by adjusting the balance of the blowers to maintain the furnace pressure is -20 ~ -30Pa. 5, the thermal efficiency of the boiler to improve the thermal efficiency of the boiler should be kept above 60%. II. Combustion Adjustment 1, the amount of fuel to air required for combustion and the amount of a reasonable distribution. Ventilation should first increase the amount of fuel increases, it should first reduce the amount of fuel supply reduced ventilation. 2, the thickness of the seam and seam thickness configuration grate speed is 80 ~ 120mm grate speed at high, middle and low profile configuration of several commonly used methods:. 9a rapid combustion of thin seam b c thick seam in low combustion. 3 thick seam combustion speed, the segment with the wind blowing principle: burn promoting intermediate ends. That is, after the coal into the coal starts to warm up the shutter, fire line front arch, the primary combustion zone, the middle grate to burn the rear grate zone. Normal combustion conditions are: fuel from the coal at the beginning of the fire shutter 300mm, uniform flames, the fire bed formation, at the end of combustion from the end of the grate 300 ~ 500mm. 4. maintain proper furnace temperature to avoid coking. The fire bed to maintain the homogeneous combustion, to avoid burning fire bed obliquely. 6. The residence time of the fuel on the grate in less than 30 minutes.Free Chat
Copyright © 2020.Company name All rights reserved.