Henan low pressure boilers seller manufacturers fuel gas combustion boiler features a contrast, combustion of fuel is a liquid fuel and fuel oil, its boiling point is always lower than the ignition point, so that fuel combustion is always performed in the gaseous state. Fuel oil particles atomized by the jet into the furnace after the furnace is heated by high temperature flue gas, gasification, and hydrocarbon ambient air encounters the oxygen gasification, a flame. Heat produced by combustion of oil particles pass a part of the gasification and combustion of oil particles continuously, until the burning ember. The smaller the diameter of oil particles, the faster the combustion of oil particles. Similarly, the oxygen required for combustion of oil particles can be supplied in time, the combustion of oil particles can more quickly. Therefore enhanced combustion of oil must do the following: 1, to improve quality of atomization, the oil particle diameter is reduced; 2, increasing the relative velocity of the air and oil particles; 3, reasonable air distribution. Second, the combustion gas boiler manufacturers Laid Henan boiler ignition gas with a high calorific value, large amount of air, can make the combustion gas, a large amount of air mixed therewith. No fuel combustion gas atomization process with the gasification process. Gas and air mixing mode, the flame length and flame temperature has a significant impact on the intensity of the combustion. Depending on the mixed mode, the combustion method of the boiler manufacturer Henan gas boiler can be divided into three types: 1, i.e., this method does not pre-mixed combustion diffusion combustion, but interdiffusion gas nozzle opening, and burned. Shao Shao stability advantages, the structure of appliance is simple, but the flame is longer, easy to produce incomplete combustion and carbonization of the heated area. 2, partially premixed combustion air prior to combustion such a way that the combustion of part of the air mixed in advance with the gas (primary air excess coefficient between 0.2-0.8), followed by combustion. The advantage is clear combustion flame, combustion strengthened, high thermal efficiency. However, combustion instability, and high combustible component of the control primary air requirements. The gas burner usually used such combustion. 3, i.e. flameless combustion air which has been uniformly mixed with the combustion gas prior to such gas required for combustion. Primary excess air ratio is equal to the excess air ratio for complete combustion of the fuel required to obtain oxygen from the ambient air during the combustion process. When the combustion gas and air mixture reaches the combustion zone can be completed in an instant.
You must know the low pressure boilers seller energy problems (induced draft fan power consumption rate, steam consumption) draft fan causes problems 1.1 boiler flue dust and fouling, in particular air preheater fouling, resulting in increased resistance to smoke duct . 1.2 boiler flue, tail heating surface and dust leakage. 1.3 Leakage Rate large air preheater. 1.4 furnace excess air coefficient is too large. 1.5 unit load changes, run the adjustment is not timely, resulting in furnace pressure is too large. 1.6 unit load or low frequent starts and stops. 1.7 coal into the furnace worse, from the design value. 1.8 low efficiency filter. 1.9 draft fan blade badly worn, low operating efficiency. 1.10 fan outlet flue gas desulfurization big resistance. 1.11 soda boiler pipes for leaks. 2, 2.1 to 2.1.1 operational measures to solve the problem of the strict implementation of soot blowing system to prevent the heated area ash, blocking ash, flue gas system to reduce resistance. 2.1.2 holding the induced draft fan, the flue gas separator baffles and dampers in the fully open position. 2.1.3 The experiment showed combustion boiler, proper control of excess air in the furnace. 2.1.4 adjustment chamber negative pressure, air leakage reduction furnace and the flue. 2.2 routine maintenance and testing 2.2.1 induced draft fan performance test to determine the optimum operating point and efficient workspace. 2.2.2 boiler, air preheater, a flue, ESP and other system leakage inspection, process. 2.2.3 timely check processing chassis, shaft seal leakage. 2.3C / D repair, eliminating defects 2.3.1 down strict accordance with movement clearance adjusting fan. 2.3.2 induced draft fan blade defect action elimination hand vane opening adjustment. 2.3.3 Importers and induced draft fan baffle opening check. 2.3.4 duct tightness check process. 2.3.5 wave plate replacement air preheater, rinsed sector plate gap adjustment. 2.3.6 eliminate dust defects and improve collection efficiency. 2.3.7 clean flue gas desulfurization system, flue resistance is reduced. 2.3.8 eliminate soda boiler pipe leakage defects. 2.4A / B repair and transformation 2.4.1 Check and repair the fan blades, replace seriously damaged blades if necessary. 2.4.2 for energy saving fan efficiency below 75%. 2.4.3 The fan motor frequency transformation. 2.4.4 of the precipitator, if necessary, transform and improve collection efficiency.
After the low pressure boilers seller high cost of it? That renovation work is currently boiler have been carried out in various provinces and cities, many users are willing to transform doubt there will be a point, that is the high cost after the boiler yet? Then we took the coal-fired gas boiler renovation project for analysis. During the transformation of the former coal-fired boilers, there will be some need for coal storage, transportation costs, low operating efficiency of the boiler, the boiler thermal efficiency loss, loss of fuel costs caused by production costs caused by the loss of non-compliance; Then there will be coal-fired processing costs pollutant emissions boiler; and a lot of maintenance costs and labor costs continue to treat boiler site troubleshooting, and accounting of these costs are relatively high. After that say transformation, gas boilers belong first and foremost clean energy, to some extent, less waste emissions, it will save some gas treatment costs; In addition, the auxiliary gas boiler system more orderly is not complicated, so the run is relatively stable , operating efficiency is relatively high, so will enhance the operational boiler thermal efficiency to a certain extent, there is some improvement on return loss and the cost of fuel; at the same time, gas boiler this would not take up space, just to ensure perimeter clean can be, relatively speaking, save some labor costs, probably in terms of fuel, natural gas will be slightly more expensive than some of the coal, but the longer term, energy-saving effect of natural gas boilers, will be a period of time, return this part of the difference in money, but if management properly, will reach back to the results. After so the cost after the boiler strictly speaking, is not elevated, a certain time, will achieve cost reduction.
It is understood that the main purpose of this research group is to study the production and operation of special equipment safety in our province, our city as a leader in the field of industrial and special equipment production areas of well-known companies has been the concern of the research group. After the tour, the research group said it would I recommend the best practices for future sample safe production, operation and management of special equipment, I also hope that the company's future and make greater achievements and contributions in the field.Free Chat
Copyright © 2020.Company name All rights reserved.