Employees to the annual meeting full of plans for our programs are presented shine. Whether sporty side fast version of "Desert Camel" was full of rhythmic Allegro "golden rice bowl", it combines the efforts and achievements we have made in 2018, exceptionally exciting. There festive set in one of the nation's lasting appeal of traditional dance "dance together" and "unforgettable beauty heart", gives us the beauty of the impact.
Gas new design warm boiler heat loss through the combustion of fuel gas boiler, will release some heat, which will supply part of the user, some will be recycled and part is inadvertently wasted. So these are wasted heat lost through the ways in which it (1) heat losses:? Flue gas exhaust gas boiler part of the heat into the atmosphere, causing the boiler heat losses, it is each boiler term heat loss Dazhong biggest one. The main factors influencing the heat loss is higher exhaust gas temperature and the amount of smoke exhaust gas temperature, the greater the amount of smoke, the greater the heat loss. Low exhaust gas temperature depends mainly on the number and operating conditions of the heating surface; the amount depends on how much leakage exhaust case and the furnace excess air, flue. (2) heat loss incomplete combustion gas: a part of the unburned combustible gas is discharged with the flue gas to heat loss caused by heat in the flue gas. The main factors affecting the incomplete combustion gas heat loss is the excess air and furnace structure. Excess air coefficient is too small, uneven air is mixed with fuel, easy to generate carbon monoxide and other combustible gases; excess air coefficient is too large, the furnace temperature is lowered, the combustible gas is not easy ignition and combustion. Furnace volume is too small, combustible gases in the furnace too late to enter the combustion flue gases caused by incomplete combustion heat loss. (3) heat loss: the furnace heat loss, frameworks, pipes, door opening caused by heat dissipation to the surroundings. Size depends on the heat loss factors of the size of the surface area of the furnace gas steam boiler, heat insulating properties and thickness, the outside air temperature and the flow velocity. Electric heating reactor common external damage: an electrically heated reactor despite external corrosion has a high etching resistance against acid and alkali resistance, but our electrical heating by the heating apparatus is a kettle layer and an outer tire iron constituted. Such a medium is iron acids and bases are not corrosion-resistant. If we would have the production process if the reactor cover or screwed pipe joints without seal failure or leak acid tire iron reactor apparatus for electrically heating the outer corrosion. Corrosion support member 2. The reactor was heated electrically heated reactor during installation, support or other support member may be mounted directly on the floor, due to the long manufacturing operations on the floor may be deposited with corrosive media, so that for support our reactor electrically heated apparatus corrosion, resulting in the supporting force of each of the support produces a change resulting in a change in stress in the damage produced during heating layer. 3. The electrically heated reactor stress spout in the electrically heated reactor, when the steel of the pipe and the pipe joint, since the thermal deformation and the reaction was heated electrically heated autoclave vessel or duct stressed cold might damage the pipe.
With the increase of air supply volume, the mixture of oil mist and air is improved, which is beneficial to combustion. However, if the air volume is too large, the furnace temperature will be decreased and the incomplete combustion loss will be increased. At the same time, the heat loss of exhaust gas will be increased and the power consumption of the fan will be increased because of the increase of flue gas. If the air volume is insufficient, the combustion will be incomplete, resulting in carbon deposition at the tail, which is prone to secondary combustion accidents. Therefore, each new design warm boiler should pass the thermal efficiency test to determine its economic air volume at different loads. In practice, the stoves usually take into account the ignition of the nozzle and the carbon dioxide or oxygen content in the flue gas. Content to adjust the supply air volume. If it is found that the combustion condition of a nozzle is not good, or if the atomization plate with different aperture is replaced, the air pressure of the supply duct should be kept unchanged, and the opening degree of the duct baffle of the nozzle should be adjusted to normal combustion. If the fuel quantity changes due to the change of the oil pressure in front of the furnace, the opening of the fan baffle should be adjusted to achieve normal combustion by changing the air pressure and air volume of the air supply duct when it is necessary to adjust the supply air volume.
3) the observation and analysis of all kinds of flame when adjusting the fuel oil. Generally through the fire point adjustment and flame center adjustment to complete the flame adjustment. The ignition point of the oil mist should be close to the nozzle, but there should be no tempering. Early ignition is beneficial to complete combustion and stability of oil mist. However, the fire is too early, too close to the nozzle, easy to burn the nozzle and furnace wall to determine the mouth. Furnace temperature flying oil varieties and atomization quality, as well as air volume, wind speed and oil temperature, will affect the distance and proximity of the ignition point. So if you want to adjust the ignition point, you should find out the cause in advance, and then take targeted measures. When the boiler load is constant and the oil pressure and oil temperature are stable, Should be based on the ignition point wind speed and wind distribution situation.
After completion of the gas new design warm boiler cleaning, be sure to use hot air to dry them, but not both for heating the furnace walls and other accessories, this is likely to have adverse consequences. Right way is to place an electric heater in the bottom of the gas boiler, heated.Free Chat
Copyright © 2020.Company name All rights reserved.