Regular inspection of new type high efficiency bioamss boilers 1, external inspection, usually once a year, this test is in the operating state of the boiler, check the safety accessories, automatic control instruments, protection devices are sensitive, reliable; joints with or without compression component leakage phenomenon; also check the relevant rules and regulations in particular the management of water quality and the implementation of the rules and regulations established. Check the contents of the existing concrete visible external inspection requirements. External inspection has a direct role in preventing accidents. 2, the internal check: every two years a transfer. This test is to conduct a comprehensive internal and external boiler inspections to stop running in the boiler state. The main defect inspecting various boiler heating surface forming operation, such as wear, corrosion, fatigue, deformation or the like, but also to check the security status of the attachment. Specific requirements visible check the current national regulations. 3, hydrostatic test: general once every six years. That can not carry out internal inspection of boilers, pressure test every three years. 1) hydrostatic test pressure should meet the following: the name of the boiler working pressure P test pressure boiler 0.8MPa1.5P, but not less than 0.2MPa boiler 0.8-1.6MPaP + 0.4MPa boiler> 1.6MPa1.25P any pressure superheater the same test pressure boiler body and separable any working pressure economizer 1.25P + 0.5MPa2) and the hydrostatic test requirements of the basic steps: the boiler pressure test, pressure should slow down. First, the cabinet lead off the burner, it can not work. When the pressure rises to the pressure of work, should be suspended boost, check for leaks and other anomalies, and then boosted to the test pressure. Boiler should be maintained for 20 minutes at the test pressure, and then down to the working pressure checked. During the inspection the pressure should remain unchanged. Hydrostatic test shall be carried out when the ambient temperature is higher than 5 ℃, antifreeze measures must be less than 5 ℃. Water pressure test should be maintained above the dew point temperature of the surrounding surfaces to prevent condensation boiler, but it should not cause the high temperature vaporization and to prevent excessive temperature stress, is generally 20 ~ 70 ℃. 3) passing the test pressure condition: 1, there is no pressure on the walls and the weld metal element and the mist droplets; 2, when the working pressure drops mouth inflation does not drip; 3, hydrostatic testing, no residual deformation was found.
Practice 1 steam new type high efficiency bioamss boiler, a monthly gauge of the trap should be washed once, check the pressure gauge is working normally and accurate. 2, coping backup water supply equipment (such as steam Chu, the water injector) once a week commissioning, ensure its good operating order. 3, each class should check the induced draft fan, grate and other bearing grease, the timely supplement. 4, during operation of the boiler should be checked regularly blower, induced draft fan, water pump and other functioning of the grate. 5, during operation of the boiler, you should always check the boiler manhole, hand hole and whether there is abnormal leakage pressure parts deformation. 6, during operation of the boiler should be checked regularly blower, induced draft fan, water pump and other functioning of the grate. 8, Stokes boiler, the boost, induced draft fan should be ventilated for 5 minutes, the remaining fuel gas discharged in the furnace and the flue. 9, should be carried out regularly sewage water level is low at high load, so that each sewage water level drops about 30 to 50 mm. 10, an exhaust valve should be manually test once a week, to prevent the valve body and the valve seat sticking, to ensure safety valve sensitive and reliable. 11, the boiler stoked speed should be slow, up to fire the furnace from a cold operating state for not less than 1--2 hours, the pressure from the fire furnace to the operating state can not be less than 0.5 hours. 12, each class should be 12 times the sewage regularly to ensure water clear, accurate, and reliable. The water level in the range of normal water level should not exceed ± 40 mm. 13, put into operation before the boiler, boiler respond, safety accessories, water supply equipment, blowers and other equipment to conduct a comprehensive examination, confirmed normal, to start boot. 14, each class should remove fouling in the boiler, wash the floor, wipe boilers, pumps, fans and other fouling, grease on the equipment, the boiler room to keep clean and civilized production. 15, during boiler operation, must closely monitor the water level, pressure and combustion conditions, the right to adjust various parameters, once per hour record run. 16, pressure fire during the night, there should be someone on duty. Check the pressure level is normal, the check whether the furnace is off or re-ignition seam so on. 17, when the supply of external steam boiler, should open the sub-cylinder, the steam trap pipe to drain the condensed water, and then slightly opening the steam supply valve heating pipe, and finally a large opening for the steam outside the steam supply valve.
Which high-quality steam new type high efficiency bioamss boiler? Boiler quality, including what? For steam boiler users, it wants its good product quality. But the quality of this product also includes many aspects, naturally, you want a user to purchase some attention. First, we need to let the good energy efficiency in use. Because the boiler itself is a type of energy product, if it is using excessive energy consumption in use, it will naturally increase the cost of ownership, so relatively speaking, such a product is difficult to be accepted by users. . But want to make products have a good use of energy efficiency, manufacturers will need to have a good technical strength.
Oriental Hawaii Holiday Hotel is located in Xiaogan City of Hubei Province in accordance with international five-star hotel standard design, set business rooms, SPA bath, foot care, indoor spa and other facilities in one of the hotel. Hot water new type high efficiency bioamss boiler is one of the important facilities normal operation can not be separated. With the pace of Hubei Province in response to the national defense of the blue sky, the use of clean fuels gradually increase the proportion of Oriental Hawaii hotel provides visitors to the more perfect leisure experience a sense of the original wishing more polluted coal-fired boilers to replace clean and green gas-fired boiler. After comparing several vendors boiler industry, a number of R & D results very fast square value in the field of clean fuels, entered into a collaboration with the fast boiler. Fast boiler integrally provided a 1.4MW condensing pressure hot water boiler (CWNSL1.4-95 / 70-Y.Q) according to their actual needs. Put into use, fully meet the needs of Oriental Hawaii Holiday Hotel heating and hot water supply.Free Chat
Copyright © 2020.Company name All rights reserved.