Burner and flue installation and electrical installation and the fuel supply system of the burner 1, burner 1) before installation read "burner manual", according to the installation requirements. 2) Burner mounting flange, the middle requirements, to ensure the burner to the fired boiler in tanzania flue gas does not leak at the interface. 2, the installation of fuel supply system (see schematic) Note: To prevent a fire caused by generation of static electricity in the fuel tank, the tank should have a good grounding. 1) supply system tank top tank top-feed system suction recommended distance between the back plane and the tubing inside diameter of the oil pump axis, the total length of the suction pipe Hm, m, no greater than DL6-34DL40-75DL100-250Di = 10mmDi = 14mmDi = 16mm0.51.03030401.535452.03535452.540503.0404050 Notes: (1) when there is an elbow or valve on the suction pipe, each of the length of the suction pipe to be minus 0.25m. (2) Di recommended internal diameter suction pipe and return pipe. 2) the distance between the bottom of the tank bottom of the tank supply system supply system pipe inner diameter recommended oil pump axis and a plane, the total length of the suction pipe Hm, m, no greater than DL6-34DL40-75DL100-250Di = 10mmDi = 14mmDi = 16mm1.03030401.535452.03535452.540503.04040504.045 Notes: (1) when there is an elbow or valve on the suction pipe, each of the length of the suction pipe to be minus 0.25m. (2) Di recommended internal diameter suction pipe and return pipe. 3, gas pipe installation requirements Burner gas line itself has been connected, the intake port, the intake pipe bends should be minimized and good sealing performance requirements, to prevent leakage. (Iv) a chimney installation, to prevent leakage, the leakage of smoke, to prevent smoke inhalation chamber. 2, a vertical mounting, a right angle bend bends should be avoided. 3, the top of the chimney must be water-resistant measures. (E) mounting a power switch with electrical connection box 1, the power switch should be considered easy to operate, away from heat, fixation, meet the design requirements. 2, the use of 220V (380V), 50HZ power source, and a ground line. 3, voltage instability in the region use, should be safe regulators. Or affect the normal operation of the combustion engine. 4, the power cord to the electrical box must be connected in strict accordance with the requirements, otherwise, there will be dangerous!
Hebei province is the use of industrial fired boiler in tanzanias, countless large and small boilers, air pollution caused by coal-fired boiler is one of the problems of governance in Hebei Province, and therefore become a major coal-fired boiler control of air pollution in Hebei Province direction. Coal-fired auxiliary boiler control work steadily, the Hebei provincial government to develop a "" comprehensive management of air pollution in Hebei provincial financial assistance fund management approach ", the boiler subsidy detailed as follows:
1, rural areas electricity instead of coal subsidies
The household equipment purchase and install (including line transformation indoor) 85% of investment subsidies, the maximum subsidy per household amount not more than 7400 yuan, the provincial and city and county respectively 50%, the rest borne by the users themselves.
Residents give electricity for heating 0.2 yuan / kwh subsidies, provincial, city and county average bear, the highest household electricity 10,000 kwh subsidies, subsidies and standards tentatively scheduled for three years.
2, substitution of gas for coal in rural areas subsidy standards
The household gas equipment purchase and install the 70% investment subsidies, the maximum subsidy per household amount not more than 2700 yuan. Provincial cities and counties and respectively 50%, the rest borne by the user.
Heating gas for customers who use 1 yuan / cubic meter of subsidy per household per year up to 1200 m3 gas subsidies, provincial, city and county average bear, subsidies and standards tentative three years.
Given the highest building in the village of pipelines family home investment subsidies of 4,000 yuan, 1000 yuan assume the provincial, city and county to bear 3,000.
3, coal-fired boiler subsidy governance standards
Subsidies for coal-fired boilers, eliminate subsidies, a separate ban demolition of 30,000 yuan / tons of steam, the implementation of clean energy transformation of 80,000 yuan / tons of steam.
4, thermal power shutting down out of subsidies
Provincial for shutting down the unit by 300 yuan / kilowatt award given up, have been included in the national "Thirteen Five." Plan for shutting down the unit, illegal construction unit, run-of-life choice except unit and power capacity index trading.
Why fuel gas-fired fired boiler in tanzania will turn off? Although the case of gas-fired boiler fuel oil dual boiler, but only that the furnace can be gas fuel, but a normal customer choice is to select a class of the final fuel only, even if a mixed gas, also belong to the category of gas.
Combustion Adjustment of dual-use oil and gas fired boiler in tanzanias (Skills) boiler firing was successful, the load can be adjusted to normal operation. At this point, we should always observe the furnace combustion, if there is a bad oil and gas atomization, beating the flame, the flame hit the furnace and the exhaust gas temperature is too high or too low and so, it is timely for oil pressure, oil temperature, of steam, wind, air pressure, steam pressure hanging line adjustments to ensure safe and economic operation of the boiler. Size and load size of hydraulic, pneumatic boiler related to the oil pressure adjusted by adjusting the back pressure or fuel burner to achieve the size, by adjusting the air pressure to achieve the degree of opening of the valve. Adjust the amount of oil, air pressure adjustment load, at the same time, air volume control, must be synchronized to ensure a reasonable match of oil and the amount of wind, so as to achieve economic operation of the boiler. 1, the combustion method of determining boiler fuel gas: C02 content is determined from the flue gases and excess air ratio (1) the combustion quality (2) determines the length of the flame from the combustion quality (3) from the flame color and smoke color determination 2 is good or bad combustion, fuel combustion boiler adjustment method: the normal combustion, furnace flame stability was white orange, generally rumble, or if the flame beating abnormal sound, should adjust the fuel and air volume. If the adjusted still no improvement, it should identify the cause flameout, the measures to be taken and re-ignition.Free Chat
Copyright © 2020.Company name All rights reserved.